zabbix_export:
  version: '5.4'
  date: '2021-11-25T12:34:43Z'
  groups:
    -
      uuid: 57b7ae836ca64446ba2c296389c009b7
      name: Templates/Modules
    -
      uuid: ba2e8b419dc34041a69c37f012749e54
      name: YourGroup
    -
      uuid: e8473f9c56b640d7b53a8b0065b93853
      name: YourGroup/YourHost
  templates:
    -
      uuid: 37e5eb5606bc4abba66c8b20381a1e8a
      template: 'Template Module ICMP Ping'
      name: 'Template Module ICMP Ping'
      description: 'Template Module ICMP Ping version: 0.12'
      groups:
        -
          name: Templates/Modules
      items:
        -
          uuid: db5a94f6cea14deba957202b2f014469
          name: 'ICMP ping'
          type: SIMPLE
          key: icmpping
          delay: '60'
          history: 1w
          valuemap:
            name: 'Service state'
          tags:
            -
              tag: Application
              value: Status
          triggers:
            -
              uuid: b030876299434f3ba43e11c584104a81
              expression: 'max(/Template Module ICMP Ping/icmpping,#3)=0'
              name: 'Unavailable by ICMP ping'
              priority: HIGH
              description: |
                Last value: {ITEM.LASTVALUE1}.
                Last three attempts returned timeout.  Please check device connectivity.
        -
          uuid: 04b21adaf422473a88df2c52786474ed
          name: 'ICMP loss'
          type: SIMPLE
          key: icmppingloss
          delay: '60'
          history: 1w
          value_type: FLOAT
          units: '%'
          tags:
            -
              tag: Application
              value: Status
          triggers:
            -
              uuid: 42c4b0310aaf4b9c8cb502542b7dea90
              expression: 'min(/Template Module ICMP Ping/icmppingloss,5m)>{$ICMP_LOSS_WARN} and min(/Template Module ICMP Ping/icmppingloss,5m)<100'
              name: 'High ICMP ping loss'
              priority: WARNING
              dependencies:
                -
                  name: 'Unavailable by ICMP ping'
                  expression: 'max(/Template Module ICMP Ping/icmpping,#3)=0'
        -
          uuid: a79e33e5fd264725b934f603fa071555
          name: 'ICMP response time'
          type: SIMPLE
          key: icmppingsec
          delay: '60'
          history: 1w
          value_type: FLOAT
          units: s
          tags:
            -
              tag: Application
              value: Status
          triggers:
            -
              uuid: 32b4d8f3eba34bd380803410111d4b7f
              expression: 'avg(/Template Module ICMP Ping/icmppingsec,5m)>{$ICMP_RESPONSE_TIME_WARN}'
              name: 'High ICMP ping response time'
              priority: WARNING
              dependencies:
                -
                  name: 'High ICMP ping loss'
                  expression: 'min(/Template Module ICMP Ping/icmppingloss,5m)>{$ICMP_LOSS_WARN} and min(/Template Module ICMP Ping/icmppingloss,5m)<100'
                -
                  name: 'Unavailable by ICMP ping'
                  expression: 'max(/Template Module ICMP Ping/icmpping,#3)=0'
      macros:
        -
          macro: '{$ICMP_LOSS_WARN}'
          value: '20'
        -
          macro: '{$ICMP_RESPONSE_TIME_WARN}'
          value: '0.15'
      valuemaps:
        -
          uuid: bdb5d65d925542eaa61c302dc40fbfe8
          name: 'Service state'
          mappings:
            -
              value: '0'
              newvalue: Down
            -
              value: '1'
              newvalue: Up
    -
      uuid: 0a13474011f34ae8a28b97fb3562eadf
      template: 'UPS - diogont'
      name: 'UPS - diogont'
      templates:
        -
          name: 'Template Module ICMP Ping'
      groups:
        -
          name: YourGroup
        -
          name: YourGroup/YourHost
      items:
        -
          uuid: bc8fdd1c018a459b8b819d9f8325c0a2
          name: Contact
          type: SNMP_AGENT
          snmp_oid: 'SNMPv2-MIB::sysContact.0'
          key: sysContact
          history: 120d
          trends: '0'
          value_type: CHAR
          inventory_link: CONTACT
          tags:
            -
              tag: Application
              value: Information(s)
        -
          uuid: d53fdd189c29413f9ee79427894d1c6f
          name: 'Software version (full)'
          type: SNMP_AGENT
          snmp_oid: 'SNMPv2-MIB::sysDescr.0'
          key: sysDescr
          history: 120d
          trends: '0'
          value_type: CHAR
          inventory_link: OS_FULL
          tags:
            -
              tag: Application
              value: Information(s)
        -
          uuid: 7e9baf65a4b3425d9a8843e09b3c0ed4
          name: 'Device Location'
          type: SNMP_AGENT
          snmp_oid: 'SNMPv2-MIB::sysLocation.0'
          key: sysLocation
          history: 120d
          trends: '0'
          value_type: CHAR
          inventory_link: LOCATION
          tags:
            -
              tag: Application
              value: Information(s)
        -
          uuid: 87924b9990544e72b92b2586b4338340
          name: 'Device Name'
          type: SNMP_AGENT
          snmp_oid: 'SNMPv2-MIB::sysName.0'
          key: sysName
          history: 120d
          trends: '0'
          value_type: CHAR
          inventory_link: NAME
          tags:
            -
              tag: Application
              value: Information(s)
        -
          uuid: be179090fe524b06b1c94725474e1a19
          name: Uptime
          type: SNMP_AGENT
          snmp_oid: 'SNMPv2-MIB::sysUpTime.0'
          key: sysUpTime
          history: 120d
          units: uptime
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.01'
          tags:
            -
              tag: Application
              value: Information(s)
        -
          uuid: d6717d138fa8403bb07353048c45328c
          name: 'UPS battery capacity (%)'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.2.4.0
          key: upsAdvBatteryCapacity
          history: 120d
          value_type: FLOAT
          units: '%'
          tags:
            -
              tag: Application
              value: Operational
        -
          uuid: f3730f937bad4cc9abfc5b31e73e51f3
          name: 'UPS battery temperature'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.2.7.0
          key: upsAdvBatteryTemperature
          history: 120d
          units: °C
          tags:
            -
              tag: Application
              value: Operational
          triggers:
            -
              uuid: 8a704189f9a641e5b550e44b9f635616
              expression: 'last(/UPS - diogont/upsAdvBatteryTemperature)>27'
              name: 'High battery temperature on {HOST.NAME}'
              status: DISABLED
              priority: HIGH
        -
          uuid: 7f13ba90456843bfb65a1cb1694b440f
          name: 'UPS input current 1'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.3.3.1.4.1
          key: upsAdvInputCurrent1
          history: 120d
          value_type: FLOAT
          units: A
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: Operational
          triggers:
            -
              uuid: 73b3f4d1171248889119925e149b14a9
              expression: 'last(/UPS - diogont/upsAdvInputCurrent1)>=200'
              name: 'High ups input current 1'
              status: DISABLED
              priority: HIGH
              description: 'Trigger for UPS input current when value is bigger or equal 200.'
            -
              uuid: a36dfd08d0a846eeb92b34a041bf0ef0
              expression: 'last(/UPS - diogont/upsAdvInputCurrent1)>=100'
              name: 'Information ups input current 1'
              status: DISABLED
              priority: INFO
              description: 'Trigger for UPS input current when value is bigger or equal 100.'
        -
          uuid: a81866746f7a4aa59ce5b65ba6286d41
          name: 'UPS input current 2'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.3.3.1.4.2
          key: upsAdvInputCurrent2
          history: 120d
          value_type: FLOAT
          units: A
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: Operational
          triggers:
            -
              uuid: 3d01f5aa4ed64d57a1c329f9c839a864
              expression: 'last(/UPS - diogont/upsAdvInputCurrent2)>=200'
              name: 'High ups input current 2'
              status: DISABLED
              priority: HIGH
              description: 'Trigger for UPS input current when value is bigger or equal 200.'
            -
              uuid: a35697266c5841018e98d0256d057e40
              expression: 'last(/UPS - diogont/upsAdvInputCurrent2)>=100'
              name: 'Information ups input current 2'
              status: DISABLED
              priority: INFO
              description: 'Trigger for UPS input current when value is bigger or equal 100.'
        -
          uuid: 38fa890ba58f44abb991af671172c499
          name: 'UPS input current 3'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.3.3.1.4.3
          key: upsAdvInputCurrent3
          history: 120d
          value_type: FLOAT
          units: A
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: Operational
          triggers:
            -
              uuid: 6618b672d31144f8a3ac6e24293e9d6d
              expression: 'last(/UPS - diogont/upsAdvInputCurrent3)>=200'
              name: 'High ups input current 3'
              status: DISABLED
              priority: HIGH
              description: 'Trigger for UPS input current when value is bigger or equal 200.'
            -
              uuid: 9c0ac00963dd4de29aceb89607203978
              expression: 'last(/UPS - diogont/upsAdvInputCurrent3)>=100'
              name: 'Information ups input current 3'
              status: DISABLED
              priority: INFO
              description: 'Trigger for UPS input current when value is bigger or equal 100.'
        -
          uuid: 2f062eba51be4669bac5013cf02eeb8d
          name: 'UPS input frequency 1'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.3.3.1.2.1
          key: upsAdvInputFrequency1
          history: 120d
          value_type: FLOAT
          units: Hz
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: Operational
          triggers:
            -
              uuid: f11aa6d31a924a23915241845e432757
              expression: |
                last(/UPS - diogont/upsAdvInputFrequency1)>=62
                or
                last(/UPS - diogont/upsAdvInputFrequency1)<=57
              name: 'High ups Input Frequency 1'
              status: DISABLED
              priority: HIGH
              description: 'Trigger for UPS input frequency when value is different 60.'
        -
          uuid: f427cb263b65418abe7f05b5bbcefdf2
          name: 'UPS input frequency 2'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.3.3.1.2.2
          key: upsAdvInputFrequency2
          history: 120d
          value_type: FLOAT
          units: Hz
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: Operational
          triggers:
            -
              uuid: a351a5c251e941b2b588c4727160c7aa
              expression: 'last(/UPS - diogont/upsAdvInputFrequency2)>=62 or last(/UPS - diogont/upsAdvInputFrequency2)<=57'
              name: 'High ups Input Frequency 2'
              status: DISABLED
              priority: HIGH
              description: 'Trigger for UPS input frequency when value is different 60.'
        -
          uuid: ccc58c32e7074533abee32fc759c2cd6
          name: 'UPS input frequency 3'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.3.3.1.2.3
          key: upsAdvInputFrequency3
          history: 120d
          value_type: FLOAT
          units: Hz
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: Operational
          triggers:
            -
              uuid: f0354d6d45524e3a845034c1d534a283
              expression: |
                last(/UPS - diogont/upsAdvInputFrequency3)>=62
                or
                last(/UPS - diogont/upsAdvInputFrequency3)<=57
              name: 'High ups Input Frequency 3'
              status: DISABLED
              priority: HIGH
              description: 'Trigger for UPS input frequency when value is different 60.'
        -
          uuid: 3a8fe299e1b0492aa05496515aad142b
          name: 'UPS input power 1'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.3.3.1.5.1
          key: upsAdvInputPower1
          history: 120d
          value_type: FLOAT
          units: W
          tags:
            -
              tag: Application
              value: Operational
          triggers:
            -
              uuid: 63b705bb9e3045dc8d2f8ebe6dedcffe
              expression: 'last(/UPS - diogont/upsAdvInputPower1)>130'
              name: 'High ups Input Power'
              status: DISABLED
              priority: HIGH
            -
              uuid: 3b35b92c4e6742919bdd96bf9ab92ad5
              expression: 'last(/UPS - diogont/upsAdvInputPower1)>80'
              name: 'Warning Ups Input Power'
              status: DISABLED
              priority: WARNING
        -
          uuid: 2ac3b65934c143a7926bcc62a5b41d20
          name: 'UPS input power 2'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.3.3.1.5.2
          key: upsAdvInputPower2
          history: 120d
          units: W
          tags:
            -
              tag: Application
              value: Operational
          triggers:
            -
              uuid: 1902e1be66704826bf2a83a14917a1ca
              expression: 'last(/UPS - diogont/upsAdvInputPower2)>130'
              name: 'UPS input power 2'
              status: DISABLED
              priority: HIGH
            -
              uuid: 79eb23672b1640e09824233351ef21f6
              expression: 'last(/UPS - diogont/upsAdvInputPower2)>=80'
              name: 'UPS input power 2'
              status: DISABLED
              priority: WARNING
        -
          uuid: 4f8330908af942d0924597ff926b10d6
          name: 'UPS input power 3'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.3.3.1.5.3
          key: upsAdvInputPower3
          history: 120d
          units: W
          tags:
            -
              tag: Application
              value: Operational
          triggers:
            -
              uuid: f2d38e30a2cb41dd886a1714197039eb
              expression: |
                last(/UPS - diogont/upsAdvInputPower3)>80 or 
                
                last(/UPS - diogont/upsAdvInputPower3) < 130
              name: 'UPS input power 3'
              status: DISABLED
              priority: WARNING
            -
              uuid: 16188ada420f4d0da4b05d7e00ab42d5
              expression: 'last(/UPS - diogont/upsAdvInputPower3)>130'
              name: 'UPS input power 3'
              status: DISABLED
              priority: HIGH
        -
          uuid: 50efac7e4a4f4e11aabe02cb275affc5
          name: 'UPS input voltage 1'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.3.3.1.3.1
          key: upsAdvInputVoltage1
          history: 120d
          value_type: FLOAT
          units: VAC
          tags:
            -
              tag: Application
              value: Operational
          triggers:
            -
              uuid: 7e81cec9d95e4522b5a38e7e9bb2c36a
              expression: |
                last(/UPS - diogont/upsAdvInputVoltage1)>264
                or
                last(/UPS - diogont/upsAdvInputVoltage1)<176
              name: 'High Ups Input voltage 1'
              status: DISABLED
              priority: HIGH
              description: 'Trigger for UPS input voltage when value is bigger than or equal 20% or less than or equal 20%'
            -
              uuid: 10b50910d4764f82a6d2bd914be567f3
              expression: 'nodata(/UPS - diogont/upsAdvInputVoltage1,600s)=1'
              name: 'SNMP Check Connect'
              opdata: 'Loss: {ITEM.LASTVALUE1}'
              priority: WARNING
            -
              uuid: ad86aa2a92064d3b8e3f4e671cfc2c45
              expression: |
                last(/UPS - diogont/upsAdvInputVoltage1)>235
                or
                last(/UPS - diogont/upsAdvInputVoltage1)<204
              name: 'Warning Ups Input voltage 1'
              status: DISABLED
              priority: WARNING
              description: 'Trigger for UPS input voltage when value is bigger than or equal 5% or less than or equal 5%'
        -
          uuid: e3d7f7ea1c9543e7a8083314afb38be8
          name: 'UPS input voltage 2'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.3.3.1.3.2
          key: upsAdvInputVoltage2
          history: 120d
          value_type: FLOAT
          units: VAC
          tags:
            -
              tag: Application
              value: Operational
          triggers:
            -
              uuid: 07e80671b2624a00bd94738d671bf1eb
              expression: |
                last(/UPS - diogont/upsAdvInputVoltage2)>264
                or
                last(/UPS - diogont/upsAdvInputVoltage2)<176
              name: 'High Ups Input voltage 2'
              status: DISABLED
              priority: HIGH
              description: 'Trigger for UPS input voltage when value is bigger than or equal 20% or less than or equal 20%'
            -
              uuid: 9ec4b41fc95547a1b0d841178ab85dd9
              expression: 'last(/UPS - diogont/upsAdvInputVoltage2)>235 or last(/UPS - diogont/upsAdvInputVoltage2)<204'
              name: 'Warning Ups Input voltage 2'
              status: DISABLED
              priority: WARNING
              description: 'Trigger for UPS input voltage when value is bigger than or equal 5% or less than or equal 5%'
        -
          uuid: 9cf330539486472186a5a16dce939ec3
          name: 'UPS input voltage 3'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.3.3.1.3.3
          key: upsAdvInputVoltage3
          history: 120d
          value_type: FLOAT
          units: VAC
          tags:
            -
              tag: Application
              value: Operational
          triggers:
            -
              uuid: 4a12be9f9dcd441886710a226b805508
              expression: |
                last(/UPS - diogont/upsAdvInputVoltage3)>264
                or
                last(/UPS - diogont/upsAdvInputVoltage3)<176
              name: 'High Ups Input voltage 3'
              status: DISABLED
              priority: HIGH
              description: 'Trigger for UPS input voltage when value is bigger than or equal 20% or less than or equal 20%'
            -
              uuid: 874e9f6d98a54d4d999a4666fee44657
              expression: 'last(/UPS - diogont/upsAdvInputVoltage3)>235 or last(/UPS - diogont/upsAdvInputVoltage3)<204'
              name: 'Warning Ups Input voltage 3'
              status: DISABLED
              priority: WARNING
              description: 'Trigger for UPS input voltage when value is bigger than or equal 5% or less than or equal 5%'
        -
          uuid: 8eb3f54e9a13489ab5140f296166ee57
          name: 'UPS output current 1'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.4.4.1.3.1
          key: upsAdvOutputCurrent1
          history: 120d
          value_type: FLOAT
          units: A
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: Operational
        -
          uuid: afbc1bc613cd456ebea957ce9eae3783
          name: 'UPS output current 2'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.4.4.1.3.2
          key: upsAdvOutputCurrent2
          history: 120d
          value_type: FLOAT
          units: A
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: Operational
        -
          uuid: b2debde02ab346a0846c144d6fe5f424
          name: 'UPS output current 3'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.4.4.1.3.3
          key: upsAdvOutputCurrent3
          history: 120d
          value_type: FLOAT
          units: A
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: Operational
        -
          uuid: 8978b80449b74a7384c99333f72c0cfd
          name: 'UPS output frequency'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.4.2.0
          key: upsAdvOutputFrequency
          history: 120d
          value_type: FLOAT
          units: Hz
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: Operational
          triggers:
            -
              uuid: 1c0069c8ae3d401fb71c7ceed16a5786
              expression: |
                last(/UPS - diogont/upsAdvOutputFrequency)>61
                or
                last(/UPS - diogont/upsAdvOutputFrequency)<59
              name: 'High ups Output Frequency'
              status: DISABLED
              priority: HIGH
              description: 'Trigger for UPS output frequency when value is different that 60.'
        -
          uuid: 6d0de94034b24917a6ba7c1926572e14
          name: 'UPS output load 1 (%)'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.4.4.1.5.1
          key: upsAdvOutputLoad1
          history: 120d
          value_type: FLOAT
          units: '%'
          tags:
            -
              tag: Application
              value: Operational
          triggers:
            -
              uuid: f2a3f0ee94e84fe083503549ca000dd7
              expression: 'last(/UPS - diogont/upsAdvOutputLoad1)>=90'
              name: 'Output load 1 Critical on {HOST.NAME}'
              status: DISABLED
              priority: HIGH
            -
              uuid: 7752bae5bbae481e95ff2aaf88d5ee69
              expression: 'last(/UPS - diogont/upsAdvOutputLoad1)>=60'
              name: 'Output load 1 Information on {HOST.NAME}'
              status: DISABLED
              priority: INFO
              description: 'Trigger for UPS output load when value is bigger or equal 60.'
        -
          uuid: 34bc1ecba8914c64adb77c88b77b9180
          name: 'UPS output load 2 (%)'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.4.4.1.5.2
          key: upsAdvOutputLoad2
          history: 120d
          value_type: FLOAT
          units: '%'
          tags:
            -
              tag: Application
              value: Operational
          triggers:
            -
              uuid: da7fd7f17a8348baa1f4e6ac44f71c47
              expression: 'last(/UPS - diogont/upsAdvOutputLoad2)>=90'
              name: 'Output load 2 Critical on {HOST.NAME}'
              status: DISABLED
              priority: HIGH
            -
              uuid: f2828952b8c24e2888b2937f1435d2cd
              expression: 'last(/UPS - diogont/upsAdvOutputLoad2)<=60'
              name: 'Output load 2 Information on {HOST.NAME}'
              status: DISABLED
              priority: INFO
              description: 'Trigger for UPS output load when value is bigger or equal 60.'
        -
          uuid: 2ada681e47c942538f2afde70dc5819a
          name: 'UPS output load 3 (%)'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.4.4.1.5.3
          key: upsAdvOutputLoad3
          history: 120d
          value_type: FLOAT
          units: '%'
          tags:
            -
              tag: Application
              value: Operational
          triggers:
            -
              uuid: 65c4f8a7215a4cf98370bb56f419b2e3
              expression: 'last(/UPS - diogont/upsAdvOutputLoad3)>=90'
              name: 'Output load 3 Critical on {HOST.NAME}'
              status: DISABLED
              priority: HIGH
            -
              uuid: 47754f5fad334cd2bf665afa25a7e71e
              expression: 'last(/UPS - diogont/upsAdvOutputLoad3)>=60'
              name: 'Output load 3 Information on {HOST.NAME}'
              status: DISABLED
              priority: INFO
              description: 'Trigger for UPS output load when value is bigger or equal 60.'
        -
          uuid: 49cf974e4caf439fbb3dd14d3193178b
          name: 'UPS output power 1'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.4.4.1.4.1
          key: upsAdvOutputPower1
          history: 120d
          value_type: FLOAT
          units: W
          tags:
            -
              tag: Application
              value: Operational
        -
          uuid: ef2aa8bd7dfb4e92acb6e6ee54653ca5
          name: 'UPS output power 2'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.4.4.1.4.2
          key: upsAdvOutputPower2
          history: 120d
          units: W
          tags:
            -
              tag: Application
              value: Operational
        -
          uuid: 505ff4a2d9864cd38f69873593f24fb0
          name: 'UPS output power 3'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.4.4.1.4.3
          key: upsAdvOutputPower3
          history: 120d
          units: W
          tags:
            -
              tag: Application
              value: Operational
        -
          uuid: 0f53aca5b3b34bcc9eb515023eb49d54
          name: 'UPS output voltage 1'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.4.4.1.2.1
          key: upsAdvOutputVoltage1
          history: 120d
          value_type: FLOAT
          units: VAC
          tags:
            -
              tag: Application
              value: Operational
          triggers:
            -
              uuid: 4b47ee5ad3a94cca895e9cf4f4d635f8
              expression: |
                last(/UPS - diogont/upsAdvOutputVoltage1)>=231
                or 
                last(/UPS - diogont/upsAdvOutputVoltage1)<=209
              name: 'Information UPS output voltage 1'
              status: DISABLED
              priority: HIGH
              description: 'Trigger for UPS output voltage when value is bigger or equal 231 or less than or equal 209..'
        -
          uuid: e499ce738f5d46e387cb99341f37e69f
          name: 'UPS output voltage 2'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.4.4.1.2.2
          key: upsAdvOutputVoltage2
          history: 120d
          value_type: FLOAT
          units: VAC
          tags:
            -
              tag: Application
              value: Operational
          triggers:
            -
              uuid: fbb3527fca3544f6ab369366f9e2fab6
              expression: |
                last(/UPS - diogont/upsAdvOutputVoltage2)>=231
                or 
                last(/UPS - diogont/upsAdvOutputVoltage2)<=209
              name: 'Information UPS output voltage 2'
              status: DISABLED
              priority: HIGH
              description: 'Trigger for UPS output voltage when value is bigger or equal 231 or less than or equal 209..'
        -
          uuid: a9c880bcf77a40b5b75d49deeb23c00d
          name: 'UPS output voltage 3'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.4.4.1.2.3
          key: upsAdvOutputVoltage3
          history: 120d
          value_type: FLOAT
          units: VAC
          tags:
            -
              tag: Application
              value: Operational
          triggers:
            -
              uuid: 56d4ade888c14acaa423c4eefb80005e
              expression: |
                last(/UPS - diogont/upsAdvOutputVoltage3)>=231
                or 
                last(/UPS - diogont/upsAdvOutputVoltage3)<=209
              name: 'Information UPS output voltage 3'
              status: DISABLED
              priority: HIGH
              description: 'Trigger for UPS output voltage when value is bigger or equal 231 or less than or equal 209.'
        -
          uuid: d7d528546ddd4c00b8ca523671b93f01
          name: 'UPS run time remaining'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.2.3.0
          key: upsAdvRunTimeRemaining
          history: 120d
          units: m
          tags:
            -
              tag: Application
              value: Operational
          triggers:
            -
              uuid: e590c32de3c346559b84b0f3f91d2752
              expression: 'last(/UPS - diogont/upsAdvRunTimeRemaining)<5'
              name: 'Run time remaining CRITICAL on {HOST.NAME}'
              status: DISABLED
              priority: DISASTER
            -
              uuid: e04538e860844fe09ecebf1f3ea49584
              expression: 'last(/UPS - diogont/upsAdvRunTimeRemaining)<10'
              name: 'Run time remaining LOW on {HOST.NAME}'
              status: DISABLED
              priority: HIGH
        -
          uuid: 42e59fda15754095acbae6dd537e4353
          name: 'UPS Alarm Input Bad'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.6.3.3
          key: upsAlarmInputBad
          history: 120d
          tags:
            -
              tag: Application
              value: alarms
        -
          uuid: 3aa6935ae5e94784922c427ed1e9583b
          name: 'UPS Alarm Output Overload'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.6.3.8
          key: upsAlarmOutputOverload
          history: 120d
          tags:
            -
              tag: Application
              value: alarms
        -
          uuid: 131102d268dc43de9e6630e1b782857f
          name: 'UPS battery status'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.2.1.33.1.2.1
          key: upsBasicBatteryStatus
          history: 120d
          valuemap:
            name: upsBatteryStatus
          tags:
            -
              tag: Application
              value: Operational
          triggers:
            -
              uuid: b63543c262fa4c28a72117938ba3e278
              expression: 'last(/UPS - diogont/upsBasicBatteryStatus)=3'
              name: 'The battery power is too low to support the load on {HOST.NAME}'
              status: DISABLED
              priority: DISASTER
        -
          uuid: 1c0dc17bef394075b132a56d33ba0bf7
          name: 'UPS time on battery'
          type: SNMP_AGENT
          snmp_oid: 1.3.6.1.2.1.33.1.2.2.0
          key: upsBasicBatteryTimeOnBattery
          history: 120d
          units: s
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.01'
          tags:
            -
              tag: Application
              value: Operational
      dashboards:
        -
          uuid: 372c05845b2a4d559b8982ff7c0f0d07
          name: 'UPS Screen'
          pages:
            -
              widgets:
                -
                  type: GRAPH_CLASSIC
                  width: '6'
                  height: '5'
                  fields:
                    -
                      type: INTEGER
                      name: source_type
                      value: '0'
                    -
                      type: GRAPH
                      name: graphid
                      value:
                        name: 'UPS Input Voltage 1'
                        host: 'UPS - diogont'
                -
                  type: GRAPH_CLASSIC
                  x: '6'
                  width: '6'
                  height: '5'
                  fields:
                    -
                      type: INTEGER
                      name: source_type
                      value: '0'
                    -
                      type: GRAPH
                      name: graphid
                      value:
                        name: 'UPS Output Voltage 1'
                        host: 'UPS - diogont'
                -
                  type: GRAPH_CLASSIC
                  x: '12'
                  width: '6'
                  height: '5'
                  fields:
                    -
                      type: INTEGER
                      name: source_type
                      value: '0'
                    -
                      type: GRAPH
                      name: graphid
                      value:
                        name: 'UPS Output Current 1'
                        host: 'UPS - diogont'
                -
                  type: GRAPH_CLASSIC
                  x: '18'
                  width: '6'
                  height: '5'
                  fields:
                    -
                      type: INTEGER
                      name: source_type
                      value: '0'
                    -
                      type: GRAPH
                      name: graphid
                      value:
                        name: 'Battery Autonomy'
                        host: 'UPS - diogont'
                -
                  type: GRAPH_CLASSIC
                  'y': '5'
                  width: '6'
                  height: '5'
                  fields:
                    -
                      type: INTEGER
                      name: source_type
                      value: '0'
                    -
                      type: GRAPH
                      name: graphid
                      value:
                        name: 'UPS Input Voltage 2'
                        host: 'UPS - diogont'
                -
                  type: GRAPH_CLASSIC
                  x: '6'
                  'y': '5'
                  width: '6'
                  height: '5'
                  fields:
                    -
                      type: INTEGER
                      name: source_type
                      value: '0'
                    -
                      type: GRAPH
                      name: graphid
                      value:
                        name: 'UPS output voltage 2'
                        host: 'UPS - diogont'
                -
                  type: GRAPH_CLASSIC
                  x: '12'
                  'y': '5'
                  width: '6'
                  height: '5'
                  fields:
                    -
                      type: INTEGER
                      name: source_type
                      value: '0'
                    -
                      type: GRAPH
                      name: graphid
                      value:
                        name: 'UPS Output Current 2'
                        host: 'UPS - diogont'
                -
                  type: GRAPH_CLASSIC
                  x: '18'
                  'y': '5'
                  width: '6'
                  height: '5'
                  fields:
                    -
                      type: INTEGER
                      name: source_type
                      value: '0'
                    -
                      type: GRAPH
                      name: graphid
                      value:
                        name: 'Battery Capacity'
                        host: 'UPS - diogont'
                -
                  type: GRAPH_CLASSIC
                  'y': '10'
                  width: '6'
                  height: '5'
                  fields:
                    -
                      type: INTEGER
                      name: source_type
                      value: '0'
                    -
                      type: GRAPH
                      name: graphid
                      value:
                        name: 'UPS Input Voltage 3'
                        host: 'UPS - diogont'
                -
                  type: GRAPH_CLASSIC
                  x: '6'
                  'y': '10'
                  width: '6'
                  height: '5'
                  fields:
                    -
                      type: INTEGER
                      name: source_type
                      value: '0'
                    -
                      type: GRAPH
                      name: graphid
                      value:
                        name: 'UPS output voltage 3'
                        host: 'UPS - diogont'
                -
                  type: GRAPH_CLASSIC
                  x: '12'
                  'y': '10'
                  width: '6'
                  height: '5'
                  fields:
                    -
                      type: INTEGER
                      name: source_type
                      value: '0'
                    -
                      type: GRAPH
                      name: graphid
                      value:
                        name: 'UPS Output Current 3'
                        host: 'UPS - diogont'
      valuemaps:
        -
          uuid: b4ee9184dfd744f4a68afe59bf3651f9
          name: upsBatteryStatus
          mappings:
            -
              value: '1'
              newvalue: unknown
            -
              value: '2'
              newvalue: batteryNormal
            -
              value: '3'
              newvalue: batteryLow
            -
              value: '4'
              newvalue: batteryDepleted
  graphs:
    -
      uuid: 8b4125c30fb0427faad6eee1c4e8adf3
      name: 'Battery Autonomy'
      width: '300'
      show_work_period: 'NO'
      show_triggers: 'NO'
      graph_items:
        -
          sortorder: '1'
          drawtype: GRADIENT_LINE
          color: FFA726
          calc_fnc: ALL
          type: GRAPH_SUM
          item:
            host: 'UPS - diogont'
            key: upsAdvRunTimeRemaining
    -
      uuid: dcf7545f20c6483891d14ae80cf1a58f
      name: 'Battery Capacity'
      width: '200'
      show_work_period: 'NO'
      show_triggers: 'NO'
      graph_items:
        -
          sortorder: '1'
          drawtype: GRADIENT_LINE
          color: 78909C
          calc_fnc: ALL
          item:
            host: 'UPS - diogont'
            key: upsAdvBatteryCapacity
    -
      uuid: f54b6476f7fa4886bef5044541384bc6
      name: 'Battery status'
      ymin_type_1: FIXED
      graph_items:
        -
          drawtype: BOLD_LINE
          color: C80000
          item:
            host: 'UPS - diogont'
            key: upsBasicBatteryStatus
    -
      uuid: dbdb1d004db44d6d96bf22e6d96e1e82
      name: 'UPS Current'
      ymin_type_1: FIXED
      graph_items:
        -
          drawtype: BOLD_LINE
          color: B71C1C
          item:
            host: 'UPS - diogont'
            key: upsAdvInputCurrent1
        -
          sortorder: '1'
          drawtype: BOLD_LINE
          color: 4444FF
          item:
            host: 'UPS - diogont'
            key: upsAdvOutputCurrent1
    -
      uuid: bceed95aa0c441bf88c5a5b3b9c80031
      name: 'UPS Frequency'
      ymin_type_1: FIXED
      graph_items:
        -
          drawtype: GRADIENT_LINE
          color: FF4000
          item:
            host: 'UPS - diogont'
            key: upsAdvOutputFrequency
    -
      uuid: d969786039214a92bb6970484f29d647
      name: 'UPS Input Voltage 1'
      width: '150'
      show_work_period: 'NO'
      show_triggers: 'NO'
      type: STACKED
      ymin_type_1: FIXED
      graph_items:
        -
          sortorder: '1'
          drawtype: GRADIENT_LINE
          color: 43A047
          item:
            host: 'UPS - diogont'
            key: upsAdvInputVoltage1
    -
      uuid: a1998629dc61486183ef08b6680acb52
      name: 'UPS Input Voltage 2'
      width: '300'
      show_work_period: 'NO'
      show_triggers: 'NO'
      ymin_type_1: FIXED
      graph_items:
        -
          sortorder: '1'
          drawtype: GRADIENT_LINE
          color: 43A047
          item:
            host: 'UPS - diogont'
            key: upsAdvInputVoltage2
    -
      uuid: 42708aad3b3d42a3a4ffd91c3c05d870
      name: 'UPS Input Voltage 3'
      width: '300'
      show_work_period: 'NO'
      show_triggers: 'NO'
      ymin_type_1: FIXED
      graph_items:
        -
          sortorder: '1'
          drawtype: GRADIENT_LINE
          color: 43A047
          calc_fnc: ALL
          item:
            host: 'UPS - diogont'
            key: upsAdvInputVoltage2
    -
      uuid: 294c3ed0eb9e409d816e3ce69a849a1f
      name: 'UPS Load'
      ymin_type_1: FIXED
      ymax_type_1: FIXED
      graph_items:
        -
          drawtype: GRADIENT_LINE
          color: 4444FF
          item:
            host: 'UPS - diogont'
            key: upsAdvOutputLoad1
    -
      uuid: 75a96708739a425f9257abcad104d496
      name: 'UPS Output Current 1'
      width: '400'
      show_work_period: 'NO'
      show_triggers: 'NO'
      type: STACKED
      graph_items:
        -
          sortorder: '1'
          drawtype: GRADIENT_LINE
          color: FFA726
          item:
            host: 'UPS - diogont'
            key: upsAdvOutputCurrent1
    -
      uuid: db5d8234e55d42c5a092828cfbf734d4
      name: 'UPS Output Current 2'
      width: '400'
      show_work_period: 'NO'
      show_triggers: 'NO'
      type: STACKED
      graph_items:
        -
          sortorder: '1'
          drawtype: GRADIENT_LINE
          color: FFA726
          item:
            host: 'UPS - diogont'
            key: upsAdvInputCurrent2
    -
      uuid: 499cf78347a149258d15fbb0386af196
      name: 'UPS Output Current 3'
      width: '400'
      ymin_type_1: FIXED
      graph_items:
        -
          sortorder: '1'
          drawtype: GRADIENT_LINE
          color: FFA726
          calc_fnc: ALL
          item:
            host: 'UPS - diogont'
            key: upsAdvInputCurrent3
    -
      uuid: 16d2231a239e4ca08d197d0d047e97e9
      name: 'UPS Outputs Currents'
      width: '600'
      ymin_type_1: FIXED
      graph_items:
        -
          sortorder: '1'
          drawtype: BOLD_LINE
          color: 4444FF
          item:
            host: 'UPS - diogont'
            key: upsAdvOutputCurrent1
        -
          sortorder: '2'
          color: FFA726
          item:
            host: 'UPS - diogont'
            key: upsAdvOutputCurrent2
        -
          sortorder: '3'
          color: FF9800
          item:
            host: 'UPS - diogont'
            key: upsAdvOutputCurrent3
    -
      uuid: 2395fb4e16824eaf8f97769d3327ac69
      name: 'UPS Outputs Voltages'
      width: '600'
      ymin_type_1: FIXED
      graph_items:
        -
          sortorder: '1'
          drawtype: BOLD_LINE
          color: 2196F3
          item:
            host: 'UPS - diogont'
            key: upsAdvOutputVoltage1
        -
          sortorder: '2'
          color: 1E88E5
          item:
            host: 'UPS - diogont'
            key: upsAdvOutputVoltage2
        -
          sortorder: '3'
          color: 1565C0
          item:
            host: 'UPS - diogont'
            key: upsAdvOutputVoltage3
    -
      uuid: 67bbbb1a7ac7429aa2374824cfb1f720
      name: 'UPS Output Voltage 1'
      width: '400'
      show_work_period: 'NO'
      show_triggers: 'NO'
      graph_items:
        -
          sortorder: '1'
          drawtype: GRADIENT_LINE
          color: 2196F3
          calc_fnc: ALL
          item:
            host: 'UPS - diogont'
            key: upsAdvOutputVoltage1
    -
      uuid: 4628535658b94c3597193722d319ced5
      name: 'UPS output voltage 2'
      width: '400'
      show_work_period: 'NO'
      show_triggers: 'NO'
      graph_items:
        -
          sortorder: '1'
          drawtype: GRADIENT_LINE
          color: 2196F3
          item:
            host: 'UPS - diogont'
            key: upsAdvOutputVoltage2
    -
      uuid: 1fce87a6dac24614aa5a60a43c6b1d75
      name: 'UPS output voltage 3'
      width: '400'
      show_work_period: 'NO'
      show_triggers: 'NO'
      graph_items:
        -
          sortorder: '1'
          drawtype: GRADIENT_LINE
          color: 2196F3
          item:
            host: 'UPS - diogont'
            key: upsAdvOutputVoltage3
    -
      uuid: e27d01cf42124213827d7eb40b98be36
      name: 'UPS Power'
      ymin_type_1: FIXED
      graph_items:
        -
          drawtype: BOLD_LINE
          color: B71C1C
          item:
            host: 'UPS - diogont'
            key: upsAdvInputPower1
        -
          sortorder: '1'
          drawtype: BOLD_LINE
          color: 4444FF
          item:
            host: 'UPS - diogont'
            key: upsAdvOutputPower1
    -
      uuid: 34a022ab6d794c6db546f02a71292bd6
      name: 'UPS Temperature'
      ymin_type_1: FIXED
      graph_items:
        -
          drawtype: GRADIENT_LINE
          color: FF0000
          item:
            host: 'UPS - diogont'
            key: upsAdvBatteryTemperature
