zabbix_export:
  version: '5.4'
  date: '2021-11-25T12:35:17Z'
  groups:
    -
      uuid: 57b7ae836ca64446ba2c296389c009b7
      name: Templates/Modules
    -
      uuid: 153256bb78be4c2ea2a934d5731d41ae
      name: Templates/UPS
  templates:
    -
      uuid: 73c5e487af28484f85c56bdaad17d36e
      template: PitON
      name: PitON
      templates:
        -
          name: 'Template Module ICMP Ping'
      groups:
        -
          name: Templates/UPS
      items:
        -
          uuid: 18cb8a373f1649f484997399e3debee8
          name: 'Number of manager to send traps'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.2.1.1.0
          key: XPPC-MIB.mconfigTrapsReceiversNum
          delay: 6h
          description: 'The number of managers to send traps to.'
          tags:
            -
              tag: Application
              value: Trap
        -
          uuid: 08a57c340e1f4c6a8e50f321f5f9decf
          name: 'Last replaced date'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.2.1.3.0
          key: XPPC-MIB.upsBaseBatteryLastReplaceDate
          delay: 6h
          trends: '0'
          value_type: TEXT
          description: 'The date when the UPS system''s batteries were last replaced in mm/dd/yy format.   For UPS models, this value is originally set in the factory.  When the UPS batteries are replaced, this value should be reset by the administrator.'
          tags:
            -
              tag: Application
              value: Battery
        -
          uuid: d8dbf5afc738457e9cc02a51913bac40
          name: 'Battery status'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.2.1.1.0
          key: XPPC-MIB.upsBaseBatteryStatus
          delay: 5m
          history: 30d
          description: 'The status of the UPS batteries. A batteryLow(3) value indicates the UPS will be unable to sustain the current load, and its services will be lost if power is not restored. The amount of run time in reserve at the time of low battery can be configured by the upsSmartConfigLowBatteryRunTime.'
          valuemap:
            name: 'XPPC-MIB::upsBaseBatteryStatus'
          tags:
            -
              tag: Application
              value: Battery
        -
          uuid: cab9f9300f244902b3a6c9c7ba665bbd
          name: 'Battery time on'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.2.1.2.0
          key: XPPC-MIB.upsBaseBatteryTimeOnBattery
          delay: 5m
          history: 30d
          units: s
          description: 'The elapsed time in seconds since the UPS has switched to battery power.'
          tags:
            -
              tag: Application
              value: Battery
        -
          uuid: b23426789ea74a5c8fc7d477268f6e3e
          name: 'Plugged devices'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.5.1.1.0
          key: XPPC-MIB.upsBaseConfigNumDevices
          delay: 6h
          description: 'The number of devices that are plugged into the UPS.'
          tags:
            -
              tag: Application
              value: Config
        -
          uuid: 9bed63a4f95e47858b344e3c8ac35e98
          name: 'Battery conserve control'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.6.1.1.0
          key: XPPC-MIB.upsBaseControlConserveBattery
          delay: 5m
          description: |
            Setting this variable to turnUpsOffToConserveBattery(2) causes a UPS on battery to be put into 'sleep' mode immediately. The (10) means suspending time(10 minutes) before turn off UPS. UPS will turn back on when utility power is restored. Attempting to turn off a UPS that is not on battery will result in a badValue error.
                                            
            Setting this value to noTurnOffUps(1) has no effect.
                                            
            The value noTurnOffUps(1) will always be returned when the variable is read.
          valuemap:
            name: 'XPPC-MIB::upsBaseControlConserveBattery'
          tags:
            -
              tag: Application
              value: Battery
        -
          uuid: c93a336c5e6a4f1da4a0110fcab88b39
          name: 'Model name'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.1.1.1.0
          key: XPPC-MIB.upsBaseIdentModel
          delay: 6h
          history: 30d
          trends: '0'
          value_type: TEXT
          description: 'The UPS model name (e.g. ''Intelligent 8000E 900VA'').'
          tags:
            -
              tag: Application
              value: General
        -
          uuid: 57bef77126144157a7cb6cfdf199217a
          name: 'UPS ID'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.1.1.2.0
          key: XPPC-MIB.upsBaseIdentUpsName
          delay: 6h
          history: 30d
          trends: '0'
          value_type: TEXT
          description: 'An 8 byte ID string identifying the UPS. This object can be set by the administrator'
          tags:
            -
              tag: Application
              value: General
        -
          uuid: 9293a25fb73f40129d9c25c0f7cd68fc
          name: 'Input phase'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.3.1.1.0
          key: XPPC-MIB.upsBaseInputPhase
          delay: 5m
          description: 'The current AC input phase.'
          tags:
            -
              tag: Application
              value: Input
        -
          uuid: 68ff81a80de949bd83ce5a977b2fd745
          name: 'Output phase'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.4.1.2.0
          key: XPPC-MIB.upsBaseOutputPhase
          delay: 5m
          description: 'The current output phase.'
          tags:
            -
              tag: Application
              value: Output
        -
          uuid: 72930c0ba03a4c0aab6c4f7c5ec5cfda
          name: 'Output status'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.4.1.1.0
          key: XPPC-MIB.upsBaseOutputStatus
          delay: 5m
          description: 'The current state of the UPS. If the UPS is unable to determine the state of the UPS this variable is set to unknown(1)'
          valuemap:
            name: 'XPPC-MIB::upsBaseOutputStatus'
          tags:
            -
              tag: Application
              value: Output
        -
          uuid: fcbf2528d9c3432b90bfacc9e80dc273
          name: 'Eenvironment humidity'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.9.1.2.0
          key: XPPC-MIB.upsEnvHumidity
          delay: 5m
          units: '%'
          description: 'The environment humidity.'
          tags:
            -
              tag: Application
              value: Environment
        -
          uuid: cb5a94c6a81e4712bb7a3eb759288092
          name: 'Environment over humidity'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.9.2.3.0
          key: XPPC-MIB.upsEnvOverHumidity
          delay: 5m
          units: '%'
          description: 'Alarm dupsAlarmOverHumidity on when the environment humidity over the value.'
          tags:
            -
              tag: Application
              value: Environment
        -
          uuid: 53055ee0e83b4cb09736af8e57bf2a17
          name: 'Environment over temperature'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.9.2.1.0
          key: XPPC-MIB.upsEnvOverTemperature
          delay: 5m
          units: °C
          description: 'Alarm dupsAlarmOverTemperature on when the environment temperature over the value.'
          tags:
            -
              tag: Application
              value: Environment
        -
          uuid: 07cb53b5ad544c08a6d39f8fb54e3584
          name: 'Environment security 1'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.9.1.5.0
          key: XPPC-MIB.upsEnvSecurity1
          delay: 5m
          description: 'Security status'
          valuemap:
            name: 'XPPC-MIB::upsNormal/Abnormal'
          tags:
            -
              tag: Application
              value: Environment
        -
          uuid: 52d1b86bd2cd437cb856d240697f5eb3
          name: 'Environment security 2'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.9.1.6.0
          key: XPPC-MIB.upsEnvSecurity2
          delay: 5m
          description: 'Security status'
          valuemap:
            name: 'XPPC-MIB::upsNormal/Abnormal'
          tags:
            -
              tag: Application
              value: Environment
        -
          uuid: 70743200a7bb470ea8fa65cc669510bd
          name: 'Environment security 3'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.9.1.7.0
          key: XPPC-MIB.upsEnvSecurity3
          delay: 5m
          description: 'Security status'
          valuemap:
            name: 'XPPC-MIB::upsNormal/Abnormal'
          tags:
            -
              tag: Application
              value: Environment
        -
          uuid: 09de64dd611543f8a552ffd65c70f88a
          name: 'Environment security 4'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.9.1.8.0
          key: XPPC-MIB.upsEnvSecurity4
          delay: 5m
          description: 'Security status'
          valuemap:
            name: 'XPPC-MIB::upsNormal/Abnormal'
          tags:
            -
              tag: Application
              value: Environment
        -
          uuid: 1bcb8173d83443d4bafcd54283bf3a80
          name: 'Environment security 5'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.9.1.9.0
          key: XPPC-MIB.upsEnvSecurity5
          delay: 5m
          description: 'Security status'
          valuemap:
            name: 'XPPC-MIB::upsNormal/Abnormal'
          tags:
            -
              tag: Application
              value: Environment
        -
          uuid: 832974943f3a406682303b04fb42eff1
          name: 'Environment security 6'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.9.1.10.0
          key: XPPC-MIB.upsEnvSecurity6
          delay: 5m
          description: 'Security status'
          valuemap:
            name: 'XPPC-MIB::upsNormal/Abnormal'
          tags:
            -
              tag: Application
              value: Environment
        -
          uuid: da24c293d49541fc9471b89c1b790011
          name: 'Environment security 7'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.9.1.11.0
          key: XPPC-MIB.upsEnvSecurity7
          delay: 5m
          description: 'Security status'
          valuemap:
            name: 'XPPC-MIB::upsNormal/Abnormal'
          tags:
            -
              tag: Application
              value: Environment
        -
          uuid: 4dd902043fae4c748fa29fee17271b01
          name: 'Environment smoke'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.9.1.4.0
          key: XPPC-MIB.upsEnvSmoke
          delay: 5m
          description: 'Smoke status'
          valuemap:
            name: 'XPPC-MIB::upsNormal/Abnormal'
          tags:
            -
              tag: Application
              value: Environment
        -
          uuid: 4f68dc5680214b9aac4526b3c90dcbd2
          name: 'Environment temperature'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.9.1.1.0
          key: XPPC-MIB.upsEnvTemperature
          delay: 5m
          units: °C
          description: 'The ambient environment temperature.'
          tags:
            -
              tag: Application
              value: Environment
        -
          uuid: 35d551475bde4ef689e2c20aeec2da8b
          name: 'Environment under humidity'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.9.2.4.0
          key: XPPC-MIB.upsEnvUnderHumidity
          delay: 5m
          units: '%'
          description: 'Alarm dupsAlarmUnderHumidity on when the environment humidity below the value'
          tags:
            -
              tag: Application
              value: Environment
        -
          uuid: 45123af541fe4d57b45bd69fdfc26225
          name: 'Environment under temperature'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.9.2.2.0
          key: XPPC-MIB.upsEnvUnderTemperature
          delay: 5m
          units: °C
          description: 'Alarm dupsAlarmUnderTemperature on when the environment temperature below the value.'
          tags:
            -
              tag: Application
              value: Environment
        -
          uuid: 559f647b8e004d0f91936dda6ce4758d
          name: 'Environment water'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.9.1.3.0
          key: XPPC-MIB.upsEnvWater
          delay: 5m
          description: 'Water status'
          valuemap:
            name: 'XPPC-MIB::upsNormal/Abnormal'
          tags:
            -
              tag: Application
              value: Environment
        -
          uuid: f5d0020dca3f487c98835f95d0bc74d6
          name: 'Control ups off'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.6.2.1.0
          key: XPPC-MIB.upsSmaControlUpsOff
          delay: 5m
          description: |
            Setting this variable to turnUpsOff(2) causes the UPS to shut off.  When in this state, the UPS will not provide output power regardless of the input line state.  The on/off switch on the UPS must be toggled for the UPS to return to operation.
                                            
            Setting this value to noTurnUpsOff(1) has no effect.
                                            
            The value noTurnUpsOff(1) will always be returned when the variable is read.
          valuemap:
            name: 'XPPC-MIB::upsSmartControlUpsOff'
          tags:
            -
              tag: Application
              value: Control
        -
          uuid: 8462eef7fd0c42c2bb36ce1a96a0e4c5
          name: 'Battery capacity'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.2.2.1.0
          key: XPPC-MIB.upsSmartBatteryCapacity
          delay: 5m
          units: '%'
          description: 'The remaining battery capacity expressed in percent of full capacity.'
          tags:
            -
              tag: Application
              value: Battery
        -
          uuid: 477e270641ef41a1b49e276e82cc50e3
          name: 'Battery current of maximum current'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.2.2.7.0
          key: XPPC-MIB.upsSmartBatteryCurrent
          delay: 5m
          units: '%'
          description: 'The current battery current expressed in percent of maximum current.'
          tags:
            -
              tag: Application
              value: Battery
        -
          uuid: 955e47b2d4ff4c39994ef3e9abb64716
          name: 'Battery full charge voltage'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.2.2.6.0
          key: XPPC-MIB.upsSmartBatteryFullChargeVoltage
          delay: 5m
          units: V
          description: 'The fully charged battery voltage of the battery system used in the UPS, expressed in tenths of a volt.'
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: Battery
        -
          uuid: f402bd22f7b74ab4b6abc95b0a617c29
          name: 'Battery replace indicator'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.2.2.5.0
          key: XPPC-MIB.upsSmartBatteryReplaceIndicator
          delay: 5m
          description: 'Indicates whether the UPS batteries need replacing.'
          valuemap:
            name: 'XPPC-MIB::upsSmartBatteryReplaceIndicator'
          tags:
            -
              tag: Application
              value: Battery
        -
          uuid: 1d49c81e3e2a400d9ff9e843d38ed7b1
          name: 'Battery time remaining'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.2.2.4.0
          key: XPPC-MIB.upsSmartBatteryRunTimeRemaining
          delay: 5m
          units: s
          description: 'The UPS battery run time remaining before battery exhaustion, in seconds.'
          tags:
            -
              tag: Application
              value: Battery
        -
          uuid: 6e4ea14193444c7c84e16690891ca928
          name: 'Battery temperature'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.2.2.3.0
          key: XPPC-MIB.upsSmartBatteryTemperature
          delay: 5m
          units: °C
          description: 'The current internal UPS temperature expressed in tenths of a Celsius degree.'
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: Battery
        -
          uuid: 43d8a8dbbbef4ab993520f662bf0b878
          name: 'Battery current voltage'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.2.2.2.0
          key: XPPC-MIB.upsSmartBatteryVoltage
          delay: 5m
          units: VDC
          description: 'The current battery voltage expressed in 1/10 VDC'
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: Battery
        -
          uuid: cdd91d1b7bb34d5e8c88f31158a6e8c9
          name: Alarm
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.5.2.4.0
          key: XPPC-MIB.upsSmartConfigAlarm
          delay: 5m
          description: 'A flag indicating how the UPS should handle audible line fail alarms.'
          valuemap:
            name: 'XPPC-MIB::upsSmartConfigAlarm'
          tags:
            -
              tag: Application
              value: Config
        -
          uuid: 5a01d4df56a14a56a3d0b2c7d9d2163a
          name: 'Alarm timer'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.5.2.5.0
          key: XPPC-MIB.upsSmartConfigAlarmTimer
          delay: 5m
          units: s
          description: |
            The time in seconds after initial line failure at which the UPS begins emitting audible alarms (beeping). This timer is observerd only if the value of extControlAlarm is timed(2). Allowed values are 0 or 30 seconds.
                                            
            If a value other than a supported value is provided in a set request, the UPS interprets it as a the next lower acceptable value.  If the provided value is lower than the lowest acceptable value, the lowest acceptable value is used.
          tags:
            -
              tag: Application
              value: Config
        -
          uuid: 48748e15c6484c0dbeeba425d82a430f
          name: 'Hight transfer voltage'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.5.2.1.0
          key: XPPC-MIB.upsSmartConfigHighTransferVolt
          delay: 5m
          units: VAC
          description: |
            The maximum line voltage in 1/10 VAC allowed before the UPS system transfers to battery backup.
            Allowed value depend on the UPS used:
            
            120 Volt units allow settings of 1290, 1320, 1350, 1380.
            100 Volt units allow settings of 1080, 1100, 1120, 1140.
            230 Volt units allow settings of 2530, 2640, 2710, 2800.
            208 Volt units allow settings of 2240, 2290, 2340, 2390.
            
            If a value other than a supported value is provided in a set request, the UPS interprets it as the next lower acceptable value.  If the provided value is lower than the lowest acceptable value, the lowest acceptable value is used.
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: Config
        -
          uuid: 9d1c0cbd27d344cc97aaeeb5710f2014
          name: 'Low battery run time'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.5.2.8.0
          key: XPPC-MIB.upsSmartConfigLowBatteryRunTime
          delay: 5m
          units: s
          description: |
            The desired run time in seconds once the low battery condition is reached.  Allowed values are 120, 300, 420, or 600 seconds.  During this time the UPS will produce a constant warning tone which can not be disabled.
                                            
            If a value other than a supported value is provided in a set request, the UPS interprets it as a the next higher acceptable value.  If the provided value is higher than the highest acceptable value, the highest acceptable value is used.
          tags:
            -
              tag: Application
              value: Config
        -
          uuid: f429312e0e2d416294412358d794878d
          name: 'Low transfer voltage'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.5.2.3.0
          key: XPPC-MIB.upsSmartConfigLowTransferVol
          delay: 5m
          units: VAC
          description: |
            The minimum line voltage in 1/10 VAC allowed before the UPS system transfers to battery backup.
            
            Allowable values depend on the UPS used:
            120 Volt units allow settings of  970, 1000, 1030, 1060.
            100 Volt units allow settings of 810, 830, 850, 870.
            230 Volt units allow settings of 1880, 1960, 2040, 2080.
            208 Volt units allow settings of 1680, 1720, 1770, 1820.
                                            
            If a value other than a supported value is provided in a set request, the UPS interprets it as a the next higher acceptable value.  If the provided value is higher than the highest acceptable value, the highest acceptable value is used.
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: Config
        -
          uuid: 4f061ebb76614510b8c53654b80043b4
          name: 'Minimim return capacity'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.5.2.6.0
          key: XPPC-MIB.upsSmartConfigMinReturnCapacity
          delay: 5m
          units: '%'
          description: |
            The minimum battery capacity as a percent of full capacity required before the UPS will return from a low battery shutdown condition.  In other words, the UPS will not re-energize the output until the battery capacity is equal to this value. Allowed values are 0, 10, 25, or 90  percent.
                                            
            If a value other than a supported value is provided in a set request, the UPS interprets it as a the next higher acceptable value.  If the provided value is higher than the highest acceptable value, the highest acceptable value is used.
          tags:
            -
              tag: Application
              value: Config
        -
          uuid: f161b7d636f5458fb0f316ec85825eac
          name: 'Rated output voltage'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.5.2.1.0
          key: XPPC-MIB.upsSmartConfigRatedOutputVoltage
          delay: 5m
          units: VAC
          description: |
            The nominal output voltage from the UPS in 1/10 VAC. Possible values are 1000, 1200, 2080, 2200, 2250, 2300 and 2400.
            NOTE: Only units that are 2200, 2250, 2300 and 2400 can be changed.  Allowable values are 2200, 2250, 2300 and 2400.
            For these adjustable units, if a value other than a supported value is provided in a set request, the UPS interprets it as the next lower acceptable value. If the provided value is lower than the lowest acceptable value, the lowest acceptable value is used.
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: Config
        -
          uuid: 0680a1c4f6c1476f87cdf9a580b5dfbc
          name: 'Return delay'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.5.2.9.0
          key: XPPC-MIB.upsSmartConfigReturnDelay
          delay: 5m
          units: s
          description: |
            The delay in seconds after utility line power returns before the UPS will turn on.  This value is also used when the UPS comes out of a reboot and before the UPS wakes up from 'sleep' mode.  Allowed values are 0, 60, 180 and 300 seconds.
                                            
            If a value other than a supported value is provided in a set request, the UPS interprets it as a the next higher acceptable value.  If the provided value is higher than the highest acceptable value, the highest acceptable value is used.
          tags:
            -
              tag: Application
              value: Config
        -
          uuid: acb2496ec61d48e69e9b863e211752d8
          name: Sensitivity
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.5.2.7.0
          key: XPPC-MIB.upsSmartConfigSensitivity
          delay: 5m
          description: 'The sensitivity of the UPS to utility line abnormalities or noises.'
          valuemap:
            name: 'XPPC-MIB::upsSmartConfigSensitivity'
          tags:
            -
              tag: Application
              value: Config
        -
          uuid: 4ed03024494a4166998451880346f39e
          name: 'Set EEPROM defaults'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.5.2.12.0
          key: XPPC-MIB.upsSmartConfigSetEEPROMDefaults
          delay: 5m
          description: |
            WRITE: Resets the UPS EEPROM variables to default values.
            READ: returns 0
          tags:
            -
              tag: Application
              value: Config
        -
          uuid: 40a0ce34e1b54ef190e75f83965267eb
          name: 'Shut off delay'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.5.2.10.0
          key: XPPC-MIB.upsSmartConfigShutoffDelay
          delay: 5m
          units: s
          description: |
            The delay in seconds the UPS remains on after being told to turn off.  Allowed values are 12, 18, 24, 30, 36, 42, 48, 54, 60, 120, 180, 240, 300, 360, 420, 480, 540, and 600 seconds.
                                            
            If a value other than a supported value is provided in a set request, the UPS interprets it as next higher acceptable value.  If the provided value is higher than the highest acceptable value, the highest acceptable value is used.
          tags:
            -
              tag: Application
              value: Config
        -
          uuid: 7ca24d3725ac4e4aa42b571e641592ee
          name: 'UPS sleep time'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.5.2.11.0
          key: XPPC-MIB.upsSmartConfigUpsSleepTime
          delay: 5m
          units: m
          description: |
            The time in minutes for the UPS to go to 'sleep' when instructed.  When in sleep mode, the UPS will not provide output power regardless of the input line state.  Once the specified time has elapsed, output power will be restored.
                                            
            This is a configuration setting.  The UPS will not go to sleep until told to do so by the manager from a management station.
                                            
            Any input value is allowed, however the UPS only recognizes 0 - 9999 minutes in one minute increments.
                                            
            If the provided value is higher than the highest acceptable value, the highest acceptable value is used.
          tags:
            -
              tag: Application
              value: Config
        -
          uuid: 66f8fed2327d4b979a61c4926952896f
          name: 'Control flash and beep'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.6.2.5.0
          key: XPPC-MIB.upsSmartControlFlashAndBeep
          delay: 5m
          description: |
            UPS to identify itself by lighting all indicators and beeping.
                                            
            Setting this variable to FlashAndBeep(2) causes the UPS lights all panel indicators and beeps.
                                            
            Setting this value to noFlashAndBeep(1) has no effect.
                                            
            The value noFlashAndBeep(1) will always be returned when the variable is read.
          valuemap:
            name: 'XPPC-MIB::upsSmartControlFlashAndBeep'
          tags:
            -
              tag: Application
              value: Control
        -
          uuid: 1b785b5647e6432094137afe85c9e4f6
          name: 'Control reboot ups'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.6.2.2.0
          key: XPPC-MIB.upsSmartControlRebootUps
          delay: 5m
          description: |
            Setting this variable to rebootUps(2) causes the UPS to shut off and turn back on.
                                            
            Setting this value to noRebootUps(1) has no effect.
                                            
            The value noRebootUps(1) will always be returned when the variable is read.
          valuemap:
            name: 'XPPC-MIB::upsSmartControlRebootUps'
          tags:
            -
              tag: Application
              value: Control
        -
          uuid: e9fab8ca385a43f592570d980e64629e
          name: 'Control simulate power fail'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.6.2.4.0
          key: XPPC-MIB.upsSmartControlSimulatePowerFail
          delay: 5m
          description: |
            Setting this variable to simulatePowerFailure(2) causes the UPS switch to battery power.
                                            
            Setting this value to noSimulatePowerFailure(1) has no effect.
                                            
            The value noSimulatePowerFailure(1) will always be returned when the variable is read.
          valuemap:
            name: 'XPPC-MIB::upsSmartControlSimulatePowerFail'
          tags:
            -
              tag: Application
              value: Control
        -
          uuid: baf537a764fd489cbe1535dc55718f8c
          name: 'Control turn on ups load'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.6.2.6.0
          key: XPPC-MIB.upsSmartControlTurnOnUpsLoad
          delay: 5m
          description: |
            Setting this variable to upsSmartControlTurnOnUpsLoad(2) causes the UPS switch back to utility power if utility power is present.
                                            
            Setting this value to noUpsSmartControlTurnOnUpsLoad(1) has no effect.
                                            
            The value noUpsSmartControlTurnOnUpsLoad(1) will always be returned when the variable is read.
          valuemap:
            name: 'XPPC-MIB::upsSmartControlTurnOnUpsLoad'
          tags:
            -
              tag: Application
              value: Control
        -
          uuid: 10da2685ae0e41bca1a38af13e49f90e
          name: 'Control ups sleep'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.6.2.3.0
          key: XPPC-MIB.upsSmartControlUpsSleep
          delay: 5m
          description: |
            Setting this variable to putUpsToSleep(2) causes the UPS to go to sleep for the time specified by upsSmartConfigUpsSleepTime.
                                            
            When in sleep mode, the UPS will not provide output power regardless of the input line state.  Once the specified time has elapsed, output power will be restored.
                                            
            Setting this value to noPutUpsToSleep(1) has no effect.
                                            
            The value noPutUpsToSleep(1) will always be returned when the variable is read.
          valuemap:
            name: 'XPPC-MIB::upsSmartControlUpsSleep'
          tags:
            -
              tag: Application
              value: Control
        -
          uuid: 5d076f6935794a31b6105fd600272537
          name: 'SNMP Proxy agent firmware revision'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.1.2.4.0
          key: XPPC-MIB.upsSmartIdentAgentFirmwareRevision
          delay: 6h
          history: 30d
          trends: '0'
          value_type: TEXT
          description: 'The firmware revision of the UPS SNMP Proxy agent.'
          tags:
            -
              tag: Application
              value: General
        -
          uuid: 5eb498a9e5604c6d88fa80e63bb27515
          name: 'Manufactured date'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.1.2.2.0
          key: XPPC-MIB.upsSmartIdentDateOfManufacture
          delay: 6h
          history: 30d
          trends: '0'
          value_type: TEXT
          description: 'The date when the UPS was manufactured in mm/dd/yy format.'
          tags:
            -
              tag: Application
              value: General
        -
          uuid: 8548f2d2ad724dfaae68bd2b2fd74969
          name: 'Firmware revision'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.1.2.1.0
          key: XPPC-MIB.upsSmartIdentFirmwareRevision
          delay: 6h
          history: 30d
          trends: '0'
          value_type: TEXT
          description: 'The firmware revision of the UPS system.'
          tags:
            -
              tag: Application
              value: General
        -
          uuid: 38c511b584294302b762a2be73be6c59
          name: 'Serial number'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.1.2.3.0
          key: XPPC-MIB.upsSmartIdentUpsSerialNumber
          delay: 6h
          history: 30d
          trends: '0'
          value_type: TEXT
          description: 'An 8-character string identifying the serial number of the UPS internal microprocessor. This number is set at the factory.  NOTE: This number does NOT correspond to the serial number on the rear of the UPS.'
          tags:
            -
              tag: Application
              value: General
        -
          uuid: 7d0605ca557544528b47c88d8c6399d0
          name: 'Input frequency'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.3.2.4.0
          key: XPPC-MIB.upsSmartInputFrequency
          delay: 5m
          units: Hz
          description: 'The current input frequency to the UPS system in 1/10 Hz.'
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: Input
        -
          uuid: 9c54ffafe3ef4846982d73d451f26ae4
          name: 'Input line fail cause'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.3.2.5.0
          key: XPPC-MIB.upsSmartInputLineFailCause
          delay: 5m
          description: 'The reason for the occurrence of the last transfer to UPS battery power.  The variable is set to noTransfer(1) if there is no transfer yet.   The variable is set to highLineVoltage(2) if the transfer to battery is caused by an over voltage greater than the high transfer voltage. The variable is set to brownout(3) if the duration of the outage is greater than five seconds and the line voltage is between 40 percent of the rated output voltage and the low transfer voltage. The variable is set to blackout(4) if the duration of the outage is greater than five seconds and the line voltage is between 40 percent of the rated output voltage and ground.  The variable is set to smallMomentarySag(5) if the duration of the outage is less than five seconds and the line voltage is between 40 percent of the rated output voltage and the low transfer voltage.  The variable is set to deepMomentarySag(6) if the duration of the outage is less than five seconds and the line voltage is between 40 percent of the rated output voltage and ground.'
          valuemap:
            name: 'XPPC-MIB::upsSmartInputLineFailCause'
          tags:
            -
              tag: Application
              value: Input
        -
          uuid: af2a7fb55bce4639b54402d544d15d0c
          name: 'Input line voltage'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.3.2.1.0
          key: XPPC-MIB.upsSmartInputLineVoltage
          delay: 5m
          units: VAC
          description: 'The current utility line voltage in 1/10 VAC'
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: Input
        -
          uuid: 6ee868847134441a937a15238da16a44
          name: 'Input maximum line voltage'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.3.2.2.0
          key: XPPC-MIB.upsSmartInputMaxLineVoltage
          delay: 5m
          units: VAC
          description: 'The maximum utility line voltage in 1/10 VAC over the previous 1 minute period.'
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: Input
        -
          uuid: 853bd173fbad477286bdf0cab66bae6f
          name: 'Input minimum line voltage'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.3.2.3.0
          key: XPPC-MIB.upsSmartInputMinLineVoltage
          delay: 5m
          units: VAC
          description: 'The minimum utility line voltage in 1/10 VAC over the previous 1 minute period.'
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: Input
        -
          uuid: a5122a0c6c13425db31b00ce8ba5661a
          name: 'Output frequency'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.4.2.2.0
          key: XPPC-MIB.upsSmartOutputFrequency
          delay: 5m
          units: Hz
          description: 'The current output frequency of the UPS system in 1/10 Hz.'
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: Output
        -
          uuid: 7e6f45febdd445408c779a29fc3d89d9
          name: 'Output load'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.4.2.3.0
          key: XPPC-MIB.upsSmartOutputLoad
          delay: 5m
          units: '%'
          description: 'The current UPS load expressed in percent of rated capacity.'
          tags:
            -
              tag: Application
              value: Output
        -
          uuid: dda0b96569384ba096be64ad2d7de535
          name: 'Output voltage'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.4.2.1.0
          key: XPPC-MIB.upsSmartOutputVoltage
          delay: 5m
          units: VAC
          description: 'The output voltage of the UPS system in 1/10 VAC.'
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: Output
        -
          uuid: 22ecf733661046af93461d7845baf671
          name: 'Test calibration date'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.7.2.8.0
          key: XPPC-MIB.upsSmartTestCalibrationDate
          delay: 6h
          trends: '0'
          value_type: TEXT
          description: 'The date the last UPS runtime calibration was performed in mm/dd/yy format.'
          tags:
            -
              tag: Application
              value: Test
        -
          uuid: 5802831350cc4ecf9b2c8253dd8de889
          name: 'Test calibration results'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.7.2.7.0
          key: XPPC-MIB.upsSmartTestCalibrationResults
          delay: 5m
          description: |
            The results of the last runtime calibration.
                                            
            Value ok(1) means a successful runtime calibration.
                                            
            Value invalidTest(2) indicates last calibration did not take place since the battery capacity was below 100 percent.
                                            
            Value calibrationInProgress(3) means a calibration is occurring now.
          valuemap:
            name: 'XPPC-MIB::upsSmartTestCalibrationResults'
          tags:
            -
              tag: Application
              value: Test
        -
          uuid: 8a15da3e985e41e5bdfb223af6deb19f
          name: 'Test diagnostics'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.7.2.2.0
          key: XPPC-MIB.upsSmartTestDiagnostics
          delay: 5m
          description: |
            Setting this variable to testDiagnostics(2) causes the UPS to perform a diagnostic self test.
                                            
            Setting this value to noTestDiagnostics(1) has no effect.
                                            
            The value noTestDiagnostics(1) will always be returned when the variable is read.
          valuemap:
            name: 'XPPC-MIB::upsSmartTestDiagnosticSchedule'
          tags:
            -
              tag: Application
              value: Test
        -
          uuid: 8df37dfa87604fe2ac43658bd5f2b661
          name: 'Test diagnostic schedule'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.7.2.1.0
          key: XPPC-MIB.upsSmartTestDiagnosticSchedule
          delay: 5m
          description: 'The UPS system''s automatic battery test schedule.'
          valuemap:
            name: 'XPPC-MIB::upsSmartTestDiagnosticSchedule'
          tags:
            -
              tag: Application
              value: Test
        -
          uuid: 032280fa332a42f5b6dd2932df791fb9
          name: 'Diagnostics results'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.7.2.3.0
          key: XPPC-MIB.upsSmartTestDiagnosticsResults
          delay: 5m
          description: 'The results of the last UPS diagnostics test performed.'
          valuemap:
            name: 'XPPC-MIB::upsSmartTestDiagnosticsResults'
          tags:
            -
              tag: Application
              value: Test
        -
          uuid: 3fb80cd762914c7c9016c86687164178
          name: 'Test indicators'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.7.2.5.0
          key: XPPC-MIB.upsSmartTestIndicators
          delay: 5m
          description: |
            Setting this variable to testIndicators(2) causes the UPS to perform a front panel indicator (lights) test.
                                            
            Setting this value to noTestIndicators(1) has no effect.
                                            
            The value noTestIndicators(1) will always be returned when the variable is read.
          valuemap:
            name: 'XPPC-MIB::upsSmartTestIndicators'
          tags:
            -
              tag: Application
              value: Test
        -
          uuid: bbb65a8a9f7347de86e597ebd5855bf3
          name: 'Last diagnostics date'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.7.2.4.0
          key: XPPC-MIB.upsSmartTestLastDiagnosticsDate
          delay: 6h
          trends: '0'
          value_type: TEXT
          description: 'The date the last UPS diagnostics test was performed in mm/dd/yy format.'
          tags:
            -
              tag: Application
              value: Test
        -
          uuid: 66ebff3e54384fd7b35c3dd10675287d
          name: 'Test runtime calibration'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.7.2.6.0
          key: XPPC-MIB.upsSmartTestRuntimeCalibration
          delay: 5m
          description: |
            Setting this variable to performCalibration(2) causes the UPS to discharge to calibrate the UPS. The test will only start if the battery capacity is 100 percent. The test runs until capacity is less than 25 percent.
                                            
            Setting this variable to cancelCurrentCalibration(3) after setting performCalibration(2) will cancel the current discharge.
                                            
            Setting this variable to noPerformCalibration(1) will have no effect.
                                            
            The value noPerformCalibration(1) will always be returned when the variable is read.
                                            
            The result of the calibration will be saved in upsSmartTestCalibrationResult.
          valuemap:
            name: 'XPPC-MIB::upsSmartTestRuntimeCalibration'
          tags:
            -
              tag: Application
              value: Test
        -
          uuid: 681ba4c529ea49179e3e1599631e89a1
          name: 'Phase battery capacity percentage'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.1.2.0
          key: XPPC-MIB.upsThreePhaseBatteryCapacityPercentage
          delay: 5m
          units: '%'
          description: 'Battery Capacity Percentage'
          tags:
            -
              tag: Application
              value: Battery
        -
          uuid: f0df810e8e084ab297bc1419c837fc9c
          name: 'Three phase battery current'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.1.4.0
          key: XPPC-MIB.upsThreePhaseBatteryCurrent
          delay: 5m
          description: 'Battery Electric Current'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 5d03680c483942f4881a4e940a55ff00
          name: 'Three phase battery temperature'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.1.5.0
          key: XPPC-MIB.upsThreePhaseBatteryTemperature
          delay: 5m
          units: °C
          description: 'Battery Temperature'
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 405d893eba424083a4f278b8f6b4d280
          name: 'Three phase battery time remain'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.1.3.0
          key: XPPC-MIB.upsThreePhaseBatteryTimeRemain
          delay: 5m
          units: m
          description: 'Battery Time Remain (unit is Minute)'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 4db5c722f66341d99b20dda076f80ae7
          name: 'Three Phase Battery Voltage'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.1.1.0
          key: XPPC-MIB.upsThreePhaseBatteryVoltage
          delay: 5m
          units: V
          description: 'Battery Voltage'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 22a8c0ad661b42d99363f3a58838537a
          name: 'Three phase bypass source frequency'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.4.1.0
          key: XPPC-MIB.upsThreePhaseBypassSourceFrequency
          delay: 5m
          units: Hz
          description: 'Bypass Frequency'
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 10e8e51db4ee47d1bdcb7789e328d2dd
          name: 'Three phase bypss source voltage R'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.4.2.0
          key: XPPC-MIB.upsThreePhaseBypssSourceVoltageR
          delay: 5m
          units: V
          description: 'Bypass VoltageR'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: aa1935b757d742d68af234049d211757
          name: 'Three phase bypss source voltage S'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.4.3.0
          key: XPPC-MIB.upsThreePhaseBypssSourceVoltageS
          delay: 5m
          units: V
          description: 'Bypass VoltageS'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 1676eda4a9ba4a6db1ecc87e3433945a
          name: 'Three phase bypss source voltage T'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.4.4.0
          key: XPPC-MIB.upsThreePhaseBypssSourceVoltageT
          delay: 5m
          units: V
          description: 'Bypass VoltageT'
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: e95062581d5b4e509c06829e879010f9
          name: 'Three phase DC and rectifier status battery status'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.5.5.0
          key: XPPC-MIB.upsThreePhaseDCandRectifierStatusBatteryStatus
          delay: 5m
          description: 'Back Status'
          valuemap:
            name: 'XPPC-MIB::upsThreePhaseDCandRectifierStatusBatteryStatus'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 61387e4912594b6faf790700bca3723c
          name: 'Three phase DC and rectifier status charge status'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.5.6.0
          key: XPPC-MIB.upsThreePhaseDCandRectifierStatusChargeStatus
          delay: 5m
          description: 'Charge Status'
          valuemap:
            name: 'XPPC-MIB::upsThreePhaseDCandRectifierStatusChargeStatus'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 2e25b582fc2c4863b550a7231c861628
          name: 'Three phase DC and rectifier status in and out'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.5.4.0
          key: XPPC-MIB.upsThreePhaseDCandRectifierStatusInAndOut
          delay: 5m
          description: 'In And Put'
          valuemap:
            name: 'XPPC-MIB::upsThreePhaseDCandRectifierStatusInAndOut'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: d9e29265fdc2450c9d7d1bd12e2521e5
          name: 'Three phase DC and rectifier status low battery'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.5.3.0
          key: XPPC-MIB.upsThreePhaseDCandRectifierStatusLowBattery
          delay: 5m
          description: 'Low Battery'
          valuemap:
            name: 'XPPC-MIB::upsThreePhaseDCandRectifierYes/No'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 1fcd0ec026e0486b8c4b5d5e416f258d
          name: 'Three phase DC and rectifier status low battery shutdown'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.5.2.0
          key: XPPC-MIB.upsThreePhaseDCandRectifierStatusLowBatteryShutdown
          delay: 5m
          description: 'Low Battery Shutdown'
          valuemap:
            name: 'XPPC-MIB::upsThreePhaseDCandRectifierYes/No'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: a63be218d3f24d40835cbc48b1a2097f
          name: 'Three phase DC and rectifier status rectifier operating'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.5.7.0
          key: XPPC-MIB.upsThreePhaseDCandRectifierStatusRecOperating
          delay: 5m
          description: 'Rectifier Operatin'
          valuemap:
            name: 'XPPC-MIB::upsThreePhaseDCandRectifierYes/No'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 8f38c45a19e94a60b3a63f02b074b845
          name: 'Three phase DC and rectifier status rectifier rotation error'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.5.1.0
          key: XPPC-MIB.upsThreePhaseDCandRectifierStatusRecRotError
          delay: 5m
          description: 'Rectifier Rotation Error'
          valuemap:
            name: 'XPPC-MIB::upsThreePhaseDCandRectifierYes/No'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 90dbbf0da7d94dad9ce757b059bebb31
          name: 'Three phase fault status bypass breaker'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.7.3.0
          key: XPPC-MIB.upsThreePhaseFaultStatusBypassBreaker
          delay: 5m
          description: 'Bypass Breaker'
          valuemap:
            name: 'XPPC-MIB::upsThreePhaseDCandRectifierYes/No'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 71eec0b5ea064167906655aae3f82898
          name: 'Three phase fault status emergency stop'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.7.1.0
          key: XPPC-MIB.upsThreePhaseFaultStatusEmergencyStop
          delay: 5m
          description: 'Emergency Stop'
          valuemap:
            name: 'XPPC-MIB::upsThreePhaseDCandRectifierYes/No'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 5b31002b95494e01981659ca60d46557
          name: 'Three phase fault status high DC shutdown'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.7.2.0
          key: XPPC-MIB.upsThreePhaseFaultStatusHighDCShutdown
          delay: 5m
          description: 'High DC Shutdown'
          valuemap:
            name: 'XPPC-MIB::upsThreePhaseDCandRectifierYes/No'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 7b38cef9f18d4ffd925a6a6216ed10a1
          name: 'Three phase fault status inverter output fail'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.7.5.0
          key: XPPC-MIB.upsThreePhaseFaultStatusInverterOutputFail
          delay: 5m
          description: 'Output Fail'
          valuemap:
            name: 'XPPC-MIB::upsThreePhaseDCandRectifierYes/No'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 106dc2d483714da5a236e687c5045102
          name: 'Three phase fault status overLoad'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.7.4.0
          key: XPPC-MIB.upsThreePhaseFaultStatusOverLoad
          delay: 5m
          description: 'Over Load'
          valuemap:
            name: 'XPPC-MIB::upsThreePhaseDCandRectifierYes/No'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 69892de93c104b93b2e4613f67734ec7
          name: 'Three phase fault status over temperature'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.7.6.0
          key: XPPC-MIB.upsThreePhaseFaultStatusOverTemperature
          delay: 5m
          description: 'Over Temperature'
          valuemap:
            name: 'XPPC-MIB::upsThreePhaseDCandRectifierYes/No'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 38e36631159045c29047293aa64ee18c
          name: 'Three phase fault status short circuit'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.7.7.0
          key: XPPC-MIB.upsThreePhaseFaultStatusShortCircuit
          delay: 5m
          description: 'Short Circuit'
          valuemap:
            name: 'XPPC-MIB::upsThreePhaseDCandRectifierYes/No'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 1fbcbb6cd2984b7a877bb7cda5811989
          name: 'Three phase input frequency'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.2.1.0
          key: XPPC-MIB.upsThreePhaseInputFrequency
          delay: 5m
          units: Hz
          description: 'Input Frequency'
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: bfb6e66b2c454d0db1910f2ab45d99fe
          name: 'Three phase input voltage R'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.2.2.0
          key: XPPC-MIB.upsThreePhaseInputVoltageR
          delay: 5m
          units: V
          description: 'Input VoltageR'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 195701d345154df1997b027fab20b82e
          name: 'Three phase input voltage S'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.2.3.0
          key: XPPC-MIB.upsThreePhaseInputVoltageS
          delay: 5m
          units: V
          description: 'Input VoltageS'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 260389139f294c75ae94a26bd0b0dd6f
          name: 'Three phase input voltage T'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.2.4.0
          key: XPPC-MIB.upsThreePhaseInputVoltageT
          delay: 5m
          units: V
          description: 'Input VoltageT'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 8d3fa333d607474f932bc60c900c0bfc
          name: 'Three phase output frequency'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.3.1.0
          key: XPPC-MIB.upsThreePhaseOutputFrequency
          delay: 5m
          units: Hz
          description: 'Output Frequency'
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 4f89d42dd7a0422187a9caa645b22237
          name: 'Three phase output load percentage R'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.3.5.0
          key: XPPC-MIB.upsThreePhaseOutputLoadPercentageR
          delay: 5m
          units: '%'
          description: 'Load PercentageR'
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: bbdaf4e33d8b4b6b95767dfb25c046cb
          name: 'Three phase output load percentage S'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.3.6.0
          key: XPPC-MIB.upsThreePhaseOutputLoadPercentageS
          delay: 5m
          units: '%'
          description: 'Load PercentageS'
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 9e74ef3be93a4521bade9915a0c4228e
          name: 'Three phase output load percentage T'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.3.7.0
          key: XPPC-MIB.upsThreePhaseOutputLoadPercentageT
          delay: 5m
          units: '%'
          description: 'Load PercentageT'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 77aa2757fe69418cb9f73519021c2523
          name: 'Three phase output voltage R'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.3.2.0
          key: XPPC-MIB.upsThreePhaseOutputVoltageR
          delay: 5m
          units: V
          description: 'Output VoltageR'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: ce4a9824b0ae47a0ab245d623bf06bd2
          name: 'Three phase output voltage S'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.3.3.0
          key: XPPC-MIB.upsThreePhaseOutputVoltageS
          delay: 5m
          units: V
          description: 'Output VoltageS'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 418c966656764957b2d23cead38b1e63
          name: 'Three phase output voltage T'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.3.4.0
          key: XPPC-MIB.upsThreePhaseOutputVoltageT
          delay: 5m
          units: V
          description: 'Output VoltageT'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 0f00ae3aa7ca40278916bb69b967506f
          name: 'Three phase rating battery voltage'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.8.7.0
          key: XPPC-MIB.upsThreePhaseRatingBatteryVoltage
          delay: 5m
          units: V
          description: 'Battery Voltage'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 331e3bd4ff85466c8cc34c05de6ebd44
          name: 'Three phase rating bypass frequency'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.8.4.0
          key: XPPC-MIB.upsThreePhaseRatingBypassFrequency
          delay: 5m
          trends: '0'
          value_type: TEXT
          description: 'Bypass Frequency'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: d8da627ac039413cb3c75f36c2b1c523
          name: 'Three phase rating bypass voltage'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.8.3.0
          key: XPPC-MIB.upsThreePhaseRatingBypassVoltage
          delay: 5m
          description: 'Bypass Voltage'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: c7b065c3932b4f96a9d01d18df465a1b
          name: 'Three phase rating output frequency'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.8.6.0
          key: XPPC-MIB.upsThreePhaseRatingOutputFrequency
          delay: 5m
          units: Hz
          description: 'Output Frequency'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 9f57334cc87148fbafcbda61f0558d38
          name: 'Three phase rating output voltage'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.8.5.0
          key: XPPC-MIB.upsThreePhaseRatingOutputVoltage
          delay: 5m
          trends: '0'
          value_type: TEXT
          description: 'Output Voltage'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 99ad2a7e371d4ab18832b669b59a72a9
          name: 'Three phase rating power'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.8.8.0
          key: XPPC-MIB.upsThreePhaseRatingPower
          delay: 5m
          trends: '0'
          value_type: TEXT
          description: 'Power Rating'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 4ce5673e5c2543c48477a2b7c33bf19b
          name: 'Three phase rating rectifier frequency'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.8.2.0
          key: XPPC-MIB.upsThreePhaseRatingRectifierFrequency
          delay: 5m
          units: Hz
          description: 'Rectifier Frequency'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: d7454bc007ef449b995fee8724aeb426
          name: 'Three phase rating rectifier voltage'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.8.1.0
          key: XPPC-MIB.upsThreePhaseRatingRectifierVoltage
          delay: 5m
          trends: '0'
          value_type: TEXT
          description: 'Rectifier Voltage'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 7a438218124d4903a9080d96b8b84af6
          name: 'Three phase UPS static switch mode'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.6.4.0
          key: XPPC-MIB.upsThreePhaseUPSStaticSwitchMode
          delay: 5m
          description: 'Switch Mode'
          valuemap:
            name: 'XPPC-MIB::upsThreePhaseUPSStaticSwitchMode'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 5a8285abaeb141ab94681a18c9615b1b
          name: 'Three phase UPS status AC status'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.6.3.0
          key: XPPC-MIB.upsThreePhaseUPSStatusACStatus
          delay: 5m
          description: 'AC Status'
          valuemap:
            name: 'XPPC-MIB::upsThreePhaseUPSStatusACStatus'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 91e3b9f47c084521bb9ed8f3cd3d3dfa
          name: 'Three phase UPS status bypass frequency fail'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.6.1.0
          key: XPPC-MIB.upsThreePhaseUPSStatusBypassFreqFail
          delay: 5m
          description: 'Bypass Status'
          valuemap:
            name: 'XPPC-MIB::upsThreePhaseDCandRectifierYes/No'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 82dff0c2f4aa4d6e95c044c0cb612433
          name: 'Three phase UPS status inverter operating'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.6.5.0
          key: XPPC-MIB.upsThreePhaseUPSStatusInverterOperating
          delay: 5m
          description: Operating
          valuemap:
            name: 'XPPC-MIB::upsThreePhaseDCandRectifierYes/No'
          tags:
            -
              tag: Application
              value: 'Three phase'
        -
          uuid: 78f52e2faff843498e3e91c41ff39b77
          name: 'Three phase UPS status manual bypass breaker'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.935.1.1.1.8.6.2.0
          key: XPPC-MIB.upsThreePhaseUPSStatusManualBypassBreaker
          delay: 5m
          description: 'Breaker Status'
          valuemap:
            name: 'XPPC-MIB::upsThreePhaseUPSStatusManualBypassBreaker'
          tags:
            -
              tag: Application
              value: 'Three phase'
      discovery_rules:
        -
          uuid: 407bb1d23715406f944047bdb5a06474
          name: Devices
          type: SNMP_AGENT
          snmp_oid: 'discovery[{#UPSDEVICEID},1.3.6.1.4.1.935.1.1.1.5.1.2.1.1,{#UPSDEVICENAME},1.3.6.1.4.1.935.1.1.1.5.1.2.1.2]'
          key: XPPC-MIB.indexOfDevice
          delay: 1h
          description: 'Discovery pluged devices'
          item_prototypes:
            -
              uuid: 9add5e4cb8954e03bec65b820c713b09
              name: 'Device {#UPSDEVICENAME} accept'
              type: SNMP_AGENT
              snmp_oid: '1.3.6.1.4.1.935.1.1.1.5.1.2.1.4.{#UPSDEVICEID}'
              key: 'XPPC-MIB[deviceAccept.{#UPSDEVICEID}]'
              delay: 5m
              description: 'An entry is added if yes, the entry is deleted if no.'
              valuemap:
                name: 'XPPC-MIB::yes/no'
              tags:
                -
                  tag: Application
                  value: Config
            -
              uuid: 98e4c4c68a424f0385a153ae21e505e1
              name: 'Device {#UPSDEVICENAME} id'
              type: SNMP_AGENT
              snmp_oid: '1.3.6.1.4.1.935.1.1.1.5.1.2.1.1.{#UPSDEVICEID}'
              key: 'XPPC-MIB[nameOfDevice.{#UPSDEVICEID}]'
              delay: 6h
              trends: '0'
              value_type: TEXT
              description: 'The index of the device that is plugged into the UPS.'
              tags:
                -
                  tag: Application
                  value: Config
            -
              uuid: 5e64daed15af4de19d84a4873184758c
              name: 'Devices {#UPSDEVICENAME} rating'
              type: SNMP_AGENT
              snmp_oid: '1.3.6.1.4.1.935.1.1.1.5.1.2.1.3.{#UPSDEVICEID}'
              key: 'XPPC-MIB[vaRatingOfDevice.{#UPSDEVICEID}]'
              delay: 5m
              description: 'The volt-amp rating of the device plugged into the UPS'
              tags:
                -
                  tag: Application
                  value: Config
        -
          uuid: f7a82310a9b443da876894a00d78199e
          name: Traps
          type: SNMP_AGENT
          snmp_oid: 'discovery[{#TRAPID},1.3.6.1.4.1.935.2.1.2.1.1]'
          key: XPPC-MIB.trapsIndex
          delay: 1h
          description: 'Discovery traps'
          item_prototypes:
            -
              uuid: 1a137d65c7f24b4083a0a7a2689470ab
              name: 'Receiver {#TRAPID} accept'
              type: SNMP_AGENT
              snmp_oid: '1.3.6.1.4.1.935.2.1.2.1.5.{#TRAPID}'
              key: 'XPPC-MIB[receiverAccept.{#TRAPID}]'
              delay: 5m
              description: 'An entry will become active if yes, and will be deleted if no.'
              valuemap:
                name: 'XPPC-MIB::yes/no'
              tags:
                -
                  tag: Application
                  value: Trap
            -
              uuid: fb0512b287404f32addeb99e8c5a69e9
              name: 'Receiver {#TRAPID} community string'
              type: SNMP_AGENT
              snmp_oid: '1.3.6.1.4.1.935.2.1.2.1.3.{#TRAPID}'
              key: 'XPPC-MIB[receiverCommunityString.{#TRAPID}]'
              delay: 6h
              trends: '0'
              value_type: TEXT
              description: 'The community name to use in the trap when sent to the manager.'
              tags:
                -
                  tag: Application
                  value: Trap
            -
              uuid: 184167f715c44c8cab68bd89c9f40b9b
              name: 'Severity level {#TRAPID}'
              type: SNMP_AGENT
              snmp_oid: '1.3.6.1.4.1.935.2.1.2.1.4.{#TRAPID}'
              key: 'XPPC-MIB[severityLevel.{#TRAPID}]'
              delay: 5m
              description: 'The severity threshold of traps to send to the manager. Traps are labeled in severity as informational(1), warning(2), severe(3). Only traps of equal or greater severity than this value are sent to the manager.'
              valuemap:
                name: 'XPPC-MIB::severityLevel'
              tags:
                -
                  tag: Application
                  value: Trap
            -
              uuid: 14f22a28dd504a9db3c1d01f4a795653
              name: 'Trap {#TRAPID} receiver address'
              type: SNMP_AGENT
              snmp_oid: '1.3.6.1.4.1.935.2.1.2.1.2.{#TRAPID}'
              key: 'XPPC-MIB[trapsReceiverAddr.{#TRAPID}]'
              delay: 6h
              trends: '0'
              value_type: TEXT
              description: 'The IP address of the manager to send a trap to.'
              tags:
                -
                  tag: Application
                  value: Trap
      macros:
        -
          macro: '{$CRITICAL_BATTERY_TIME}'
          value: 20m
        -
          macro: '{$CRITYICAL_BATTERY_CAPACITY}'
          value: '50'
      valuemaps:
        -
          uuid: 01e9606bca4144e5aa6b975cb88d8e5f
          name: 'XPPC-MIB::severityLevel'
          mappings:
            -
              value: '1'
              newvalue: information
            -
              value: '2'
              newvalue: warning
            -
              value: '3'
              newvalue: severe
        -
          uuid: b399702438dd40a2899be6cec457e711
          name: 'XPPC-MIB::upsBaseBatteryStatus'
          mappings:
            -
              value: '1'
              newvalue: unknown
            -
              value: '2'
              newvalue: batteryNormal
            -
              value: '3'
              newvalue: batteryLow
        -
          uuid: b87e11403e56489b88cbbe0d45e5d62a
          name: 'XPPC-MIB::upsBaseControlConserveBattery'
          mappings:
            -
              value: '1'
              newvalue: noTurnOffUps
            -
              value: '2'
              newvalue: turnUpsOffToConserveBattery
            -
              value: '3'
              newvalue: turnUpsOffToConserveBatteryDelay
        -
          uuid: 41123e5301d54f03b03cd07ad9e70a89
          name: 'XPPC-MIB::upsBaseOutputStatus'
          mappings:
            -
              value: '1'
              newvalue: unknown
            -
              value: '2'
              newvalue: onLine
            -
              value: '3'
              newvalue: onBattery
            -
              value: '4'
              newvalue: onBoost
            -
              value: '5'
              newvalue: sleeping
            -
              value: '6'
              newvalue: onBypass
            -
              value: '7'
              newvalue: rebooting
            -
              value: '8'
              newvalue: standBy
            -
              value: '9'
              newvalue: onBuck
        -
          uuid: 98c134a70c894463beef4d931f64a056
          name: 'XPPC-MIB::upsNormal/Abnormal'
          mappings:
            -
              value: '1'
              newvalue: normal
            -
              value: '2'
              newvalue: abnormal
        -
          uuid: bfefbc36fe6f4317ac6631369d2dedf1
          name: 'XPPC-MIB::upsSmartBatteryReplaceIndicator'
          mappings:
            -
              value: '1'
              newvalue: noBatteryNeedsReplacing
            -
              value: '2'
              newvalue: batteryNeedsReplacing
        -
          uuid: a03411473d9f454ca0d43cc66d6f7209
          name: 'XPPC-MIB::upsSmartConfigAlarm'
          mappings:
            -
              value: '1'
              newvalue: timed
            -
              value: '2'
              newvalue: atLowBattery
            -
              value: '3'
              newvalue: never
        -
          uuid: fea0afa5e7764a77a24751ccdb7b8b62
          name: 'XPPC-MIB::upsSmartConfigSensitivity'
          mappings:
            -
              value: '1'
              newvalue: auto
            -
              value: '2'
              newvalue: low
            -
              value: '3'
              newvalue: medium
            -
              value: '4'
              newvalue: high
        -
          uuid: c99b8822aeab45119eee263d0d50c986
          name: 'XPPC-MIB::upsSmartControlFlashAndBeep'
          mappings:
            -
              value: '1'
              newvalue: noFlashAndBeep
            -
              value: '2'
              newvalue: flashAndBeep
        -
          uuid: 392e07ee7bb041c1ab3c3ada15431522
          name: 'XPPC-MIB::upsSmartControlRebootUps'
          mappings:
            -
              value: '1'
              newvalue: noRebootUps
            -
              value: '2'
              newvalue: rebootUps
        -
          uuid: 42e3769032814092a604d781f2c3f313
          name: 'XPPC-MIB::upsSmartControlSimulatePowerFail'
          mappings:
            -
              value: '1'
              newvalue: noSimulatePowerFailure
            -
              value: '2'
              newvalue: simulatePowerFailure
        -
          uuid: c6883d1f7c8f413baadc0a762ac278b7
          name: 'XPPC-MIB::upsSmartControlTurnOnUpsLoad'
          mappings:
            -
              value: '1'
              newvalue: noUpsSmartControlTurnOnUpsLoad
            -
              value: '2'
              newvalue: upsSmartControlTurnOnUpsLoad
        -
          uuid: e383c4ff15334386baf3b56cde128427
          name: 'XPPC-MIB::upsSmartControlUpsOff'
          mappings:
            -
              value: '1'
              newvalue: noTurnUpsOff
            -
              value: '2'
              newvalue: turnUpsOff
        -
          uuid: 9881e24042674cef9f827c9e83f06246
          name: 'XPPC-MIB::upsSmartControlUpsSleep'
          mappings:
            -
              value: '1'
              newvalue: noPutUpsToSleep
            -
              value: '2'
              newvalue: putUpsToSleep
        -
          uuid: 577d776b9d1147dc8c86e0c24ea28a9e
          name: 'XPPC-MIB::upsSmartInputLineFailCause'
          mappings:
            -
              value: '1'
              newvalue: noTransfer
            -
              value: '2'
              newvalue: highLineVoltage
            -
              value: '3'
              newvalue: brownout
            -
              value: '4'
              newvalue: blackout
            -
              value: '5'
              newvalue: smallMomentarySag
            -
              value: '6'
              newvalue: deepMomentarySag
            -
              value: '7'
              newvalue: smallMomentarySpike
            -
              value: '8'
              newvalue: largeMomentarySpike
        -
          uuid: 4bac9ddc53cb45948538ce6ba1cd25ec
          name: 'XPPC-MIB::upsSmartTestCalibrationResults'
          mappings:
            -
              value: '1'
              newvalue: ok
            -
              value: '2'
              newvalue: invalidTest
            -
              value: '3'
              newvalue: calibrationInProgress
        -
          uuid: 26ee15147ce9458889867b4155c14807
          name: 'XPPC-MIB::upsSmartTestDiagnosticSchedule'
          mappings:
            -
              value: '1'
              newvalue: unknown
            -
              value: '2'
              newvalue: biweekly
            -
              value: '3'
              newvalue: weekly
            -
              value: '4'
              newvalue: never
        -
          uuid: 8f26774e9d074ec9995498db7cd10e13
          name: 'XPPC-MIB::upsSmartTestDiagnosticsResults'
          mappings:
            -
              value: '1'
              newvalue: ok
            -
              value: '2'
              newvalue: failed
            -
              value: '3'
              newvalue: invalidTest
            -
              value: '4'
              newvalue: testInProgress
        -
          uuid: 458924c1b53a4c668e0b1ffa04363267
          name: 'XPPC-MIB::upsSmartTestIndicators'
          mappings:
            -
              value: '1'
              newvalue: noTestIndicators
            -
              value: '2'
              newvalue: testIndicators
        -
          uuid: f576988e99234107b0ea4f81c8b14ffd
          name: 'XPPC-MIB::upsSmartTestRuntimeCalibration'
          mappings:
            -
              value: '1'
              newvalue: noPerformCalibration
            -
              value: '2'
              newvalue: performCalibration
            -
              value: '3'
              newvalue: cancelCurrentCalibration
        -
          uuid: 0c74ca21f9ff417987005cc91199e244
          name: 'XPPC-MIB::upsThreePhaseDCandRectifierStatusBatteryStatus'
          mappings:
            -
              value: '4'
              newvalue: backup
            -
              value: '5'
              newvalue: acnormal
        -
          uuid: 5b03177d8f234c6491cd1e055d86b991
          name: 'XPPC-MIB::upsThreePhaseDCandRectifierStatusChargeStatus'
          mappings:
            -
              value: '6'
              newvalue: boost
            -
              value: '7'
              newvalue: float
            -
              value: '16'
              newvalue: 'no'
        -
          uuid: 883d565dea304548b845157b13581eb6
          name: 'XPPC-MIB::upsThreePhaseDCandRectifierStatusInAndOut'
          mappings:
            -
              value: '2'
              newvalue: threeInOneOut
            -
              value: '3'
              newvalue: threeInThreeOut
        -
          uuid: 013d736de5f147409ce7eb1033d1b347
          name: 'XPPC-MIB::upsThreePhaseDCandRectifierYes/No'
          mappings:
            -
              value: '14'
              newvalue: 'yes'
            -
              value: '16'
              newvalue: 'no'
        -
          uuid: bccde074f6ed402cb7a815b591dedad3
          name: 'XPPC-MIB::upsThreePhaseUPSStaticSwitchMode'
          mappings:
            -
              value: '12'
              newvalue: invermode
            -
              value: '13'
              newvalue: bypassmode
        -
          uuid: e02abfd9f46e4dfca08f77ef05bd1beb
          name: 'XPPC-MIB::upsThreePhaseUPSStatusACStatus'
          mappings:
            -
              value: '10'
              newvalue: normal
            -
              value: '11'
              newvalue: abnormal
        -
          uuid: cf97968204a6431fa4edbfda601bd781
          name: 'XPPC-MIB::upsThreePhaseUPSStatusManualBypassBreaker'
          mappings:
            -
              value: '8'
              newvalue: close
            -
              value: '9'
              newvalue: open
        -
          uuid: 626d04e0a4174096acb0c3c66dc15a81
          name: 'XPPC-MIB::yes/no'
          mappings:
            -
              value: '1'
              newvalue: 'yes'
            -
              value: '2'
              newvalue: 'no'
    -
      uuid: 37e5eb5606bc4abba66c8b20381a1e8a
      template: 'Template Module ICMP Ping'
      name: 'Template Module ICMP Ping'
      description: 'Template Module ICMP Ping version: 0.12'
      groups:
        -
          name: Templates/Modules
      items:
        -
          uuid: db5a94f6cea14deba957202b2f014469
          name: 'ICMP ping'
          type: SIMPLE
          key: icmpping
          delay: '60'
          history: 1w
          valuemap:
            name: 'Service state'
          tags:
            -
              tag: Application
              value: Status
          triggers:
            -
              uuid: b030876299434f3ba43e11c584104a81
              expression: 'max(/Template Module ICMP Ping/icmpping,#3)=0'
              name: 'Unavailable by ICMP ping'
              priority: HIGH
              description: |
                Last value: {ITEM.LASTVALUE1}.
                Last three attempts returned timeout.  Please check device connectivity.
        -
          uuid: 04b21adaf422473a88df2c52786474ed
          name: 'ICMP loss'
          type: SIMPLE
          key: icmppingloss
          delay: '60'
          history: 1w
          value_type: FLOAT
          units: '%'
          tags:
            -
              tag: Application
              value: Status
          triggers:
            -
              uuid: 42c4b0310aaf4b9c8cb502542b7dea90
              expression: 'min(/Template Module ICMP Ping/icmppingloss,5m)>{$ICMP_LOSS_WARN} and min(/Template Module ICMP Ping/icmppingloss,5m)<100'
              name: 'High ICMP ping loss'
              priority: WARNING
              dependencies:
                -
                  name: 'Unavailable by ICMP ping'
                  expression: 'max(/Template Module ICMP Ping/icmpping,#3)=0'
        -
          uuid: a79e33e5fd264725b934f603fa071555
          name: 'ICMP response time'
          type: SIMPLE
          key: icmppingsec
          delay: '60'
          history: 1w
          value_type: FLOAT
          units: s
          tags:
            -
              tag: Application
              value: Status
          triggers:
            -
              uuid: 32b4d8f3eba34bd380803410111d4b7f
              expression: 'avg(/Template Module ICMP Ping/icmppingsec,5m)>{$ICMP_RESPONSE_TIME_WARN}'
              name: 'High ICMP ping response time'
              priority: WARNING
              dependencies:
                -
                  name: 'High ICMP ping loss'
                  expression: 'min(/Template Module ICMP Ping/icmppingloss,5m)>{$ICMP_LOSS_WARN} and min(/Template Module ICMP Ping/icmppingloss,5m)<100'
                -
                  name: 'Unavailable by ICMP ping'
                  expression: 'max(/Template Module ICMP Ping/icmpping,#3)=0'
      macros:
        -
          macro: '{$ICMP_LOSS_WARN}'
          value: '20'
        -
          macro: '{$ICMP_RESPONSE_TIME_WARN}'
          value: '0.15'
      valuemaps:
        -
          uuid: bdb5d65d925542eaa61c302dc40fbfe8
          name: 'Service state'
          mappings:
            -
              value: '0'
              newvalue: Down
            -
              value: '1'
              newvalue: Up
