zabbix_export:
  version: '5.4'
  date: '2021-11-25T12:34:49Z'
  groups:
    -
      uuid: 7df96b18c230490a9a0a9e2307226338
      name: Templates
    -
      uuid: 57b7ae836ca64446ba2c296389c009b7
      name: Templates/Modules
  templates:
    -
      uuid: 6a07602c120f4644b2d003720978b987
      template: 'SNMP Tripp Lite PDU 15'
      name: 'SNMP Tripp Lite PDU 15'
      templates:
        -
          name: 'Template Module ICMP Ping'
      groups:
        -
          name: Templates
      items:
        -
          uuid: 67c73a5862ef44d586a79705983de3a6
          name: 'SNMP traps (fallback)'
          type: SNMP_TRAP
          key: snmptrap.fallback
          delay: '0'
          history: '{$HISTORY}'
          trends: '0'
          value_type: LOG
          logtimefmt: 'hh:mm:sszyyyy/MM/dd'
          tags:
            -
              tag: Application
              value: 'SNMP Traps'
        -
          uuid: eff41b24a6f2434da2375d163aed7259
          name: 'Agent Software Version'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.850.1.2.1.1.2.0
          key: tlpAgentVersion
          delay: '86400'
          history: '{$HISTORY}'
          trends: '0'
          value_type: CHAR
          description: 'The UPS agent software version.  This variable may or may not have the same value as upsIdentUPSSoftwareVersion in some implementations.'
          tags:
            -
              tag: Application
              value: PDU
        -
          uuid: 835b5627750a4242b37b8acdab1a4761
          name: 'Low Transfer Voltage'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.850.1.1.3.4.5.5.1.7.1.1
          key: tlpAtsConfigLowVoltageTransfer
          delay: '{$UPDATEINT}'
          history: '{$HISTORY}'
          trends: '{$TRENDS}'
          value_type: FLOAT
          description: 'The number of input voltages. Phase to phase or phase to neutral.  This variable indicates the number of rows in the input table.'
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: PDU
        -
          uuid: 69000cc5276646488312fe0b86554c99
          name: 'Input - Frequency'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.850.1.1.3.4.3.1.2.1.4.1.1.2
          key: tlpAtsInputPhaseFrequency
          delay: '{$UPDATEINT}'
          history: '{$HISTORY}'
          trends: '{$TRENDS}'
          value_type: FLOAT
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: PDU
        -
          uuid: 43cf9f3508ca42b78bc902862ef458f3
          name: 'Input - Voltage'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.850.1.1.3.4.3.1.2.1.5.1.1.1
          key: tlpAtsInputPhaseVoltage
          delay: '{$UPDATEINT}'
          history: '{$HISTORY}'
          trends: '{$TRENDS}'
          value_type: FLOAT
          description: 'The number of input voltages. Phase to phase or phase to neutral.  This variable indicates the number of rows in the input table.'
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: PDU
          triggers:
            -
              uuid: d5ce229fedde4b4aa56768e578ae4154
              expression: 'last(/SNMP Tripp Lite PDU 15/tlpAtsInputPhaseVoltage)>{$MAX_INPUTVOLTAGE}'
              name: 'PDU Power Voltage Too High'
              priority: HIGH
            -
              uuid: febfd7481d6245748d24329c8bd90b40
              expression: 'last(/SNMP Tripp Lite PDU 15/tlpAtsInputPhaseVoltage)<{$MIN_INPUTVOLTAGE}'
              name: 'PDU Power Voltage Too Low'
              priority: HIGH
        -
          uuid: 56f3641b524c49038a6c5185986fafd4
          name: 'Maximum Input Voltage'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.850.1.1.3.4.3.1.2.1.7.1.1.1
          key: tlpAtsInputPhaseVoltageMax
          delay: '{$UPDATEINT}'
          history: '{$HISTORY}'
          trends: '{$TRENDS}'
          value_type: FLOAT
          description: 'The number of input voltages. Phase to phase or phase to neutral.  This variable indicates the number of rows in the input table.'
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: PDU
        -
          uuid: 166ea628ff344537a8aaed7b45bca249
          name: 'Input - Source Availability'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.850.1.1.3.4.3.1.1.1.12.1
          key: tlpAtsInputSourceAvailability
          delay: 30s
          trends: '0'
          value_type: CHAR
          description: 'Reports power input sources for PDU.'
          tags:
            -
              tag: Application
              value: PDU
          triggers:
            -
              uuid: 85aaed357e514c97abedddc1861e667d
              expression: 'last(/SNMP Tripp Lite PDU 15/tlpAtsInputSourceAvailability)<3'
              name: 'PDU Lost Input Redundancy'
              priority: HIGH
              description: 'PDU has lost power redundancy. An input has failed.'
        -
          uuid: 1dfe2cd7163d472ab198c0bf431ccf03
          name: 'Output Current'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.850.1.1.3.4.3.2.1.1.5.1.1
          key: tlpAtsOutputCurrent
          delay: '{$UPDATEINT}'
          history: '{$HISTORY}'
          trends: '{$TRENDS}'
          value_type: FLOAT
          units: Amps
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.01'
          tags:
            -
              tag: Application
              value: PDU
          triggers:
            -
              uuid: fadffcde086f4a4197693eca172c1e24
              expression: 'last(/SNMP Tripp Lite PDU 15/tlpAtsOutputCurrent)>{$MAX_OUTPUTCURRENT_CRITICAL}'
              name: 'PDU Current Output Reaching Limit'
              priority: HIGH
            -
              uuid: 82b00444baae4d20a18f3d3159141be1
              expression: 'last(/SNMP Tripp Lite PDU 15/tlpAtsOutputCurrent)>{$MAX_OUTPUTCURRENT_WARNING}'
              name: 'PDU Current Output Too High'
              priority: WARNING
        -
          uuid: f2d020d88f464dc1aa4445cf6b2d4d6f
          name: 'Maximum Output Current'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.850.1.1.3.4.3.2.1.1.7.1.1
          key: tlpAtsOutputCurrentMax
          delay: '{$UPDATEINT}'
          history: '{$HISTORY}'
          trends: '{$TRENDS}'
          value_type: FLOAT
          units: Amps
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.01'
          tags:
            -
              tag: Application
              value: PDU
        -
          uuid: 6ce825910a4e4355bb2793630247e823
          name: 'Minimum Input Voltage'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.850.1.1.3.4.3.2.1.1.6.1.1
          key: tlpAtsOutputCurrentMin
          delay: '{$UPDATEINT}'
          history: '{$HISTORY}'
          trends: '{$TRENDS}'
          value_type: FLOAT
          description: 'The number of input voltages. Phase to phase or phase to neutral.  This variable indicates the number of rows in the input table.'
          preprocessing:
            -
              type: MULTIPLIER
              parameters:
                - '0.1'
          tags:
            -
              tag: Application
              value: PDU
        -
          uuid: f3b1c64b14fc4dafa89cf22102675e64
          name: 'PDU  Software Version'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.850.1.1.2.1.1.4.1
          key: tlpDeviceIdentFirmwareVersion
          delay: '86400'
          history: '{$HISTORY}'
          trends: '0'
          value_type: CHAR
          description: 'The UPS firmware/software version(s).  This variable may or may not have the same value as upsIdentAgentSoftwareVersion in some implementations.'
          tags:
            -
              tag: Application
              value: PDU
        -
          uuid: a13281f029334aee93c8f79e70f093ee
          name: 'PDU Serial Number'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.850.1.1.2.1.1.5.1
          key: tlpDeviceIdentSerialNum
          delay: '86400'
          history: '{$HISTORY}'
          trends: '0'
          value_type: CHAR
          description: 'Serial number for the UPS.'
          tags:
            -
              tag: Application
              value: PDU
        -
          uuid: 842e7dfcd69c46e1a7c32fbae5f59024
          name: 'Device Location'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.850.1.1.1.2.1.8.1
          key: tlpDeviceLocation
          delay: '86400'
          history: '{$HISTORY}'
          trends: '0'
          value_type: CHAR
          description: 'The device location string.'
          tags:
            -
              tag: Application
              value: PDU
        -
          uuid: ba6b882aacde47368c3a19b7bc4531cf
          name: 'Manufacturer Identification'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.850.1.1.1.2.1.4.1
          key: tlpDeviceManufacturer
          delay: '86400'
          history: '{$HISTORY}'
          trends: '0'
          value_type: CHAR
          description: 'The name of the UPS manufacturer.'
          tags:
            -
              tag: Application
              value: PDU
        -
          uuid: f2db55972b5e493ea7e902795068e2c9
          name: 'Model Identification'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.850.1.1.1.2.1.5.1
          key: tlpDeviceModel
          delay: '86400'
          history: '{$HISTORY}'
          trends: '0'
          value_type: CHAR
          description: 'The UPS Model designation.'
          tags:
            -
              tag: Application
              value: PDU
        -
          uuid: 3f7397a5f3d7485ca759c4553197819e
          name: 'Device Name'
          type: SNMP_AGENT
          snmp_oid: .1.3.6.1.4.1.850.1.1.1.2.1.6.1
          key: tlpDeviceName
          delay: '86400'
          history: '{$HISTORY}'
          trends: '0'
          value_type: CHAR
          description: 'A string identifying the UPS.  This object should be set by the administrator.'
          tags:
            -
              tag: Application
              value: PDU
      discovery_rules:
        -
          uuid: 9ffd8961cda6499089e95f54ff99e369
          name: Outlets
          type: SNMP_AGENT
          snmp_oid: 'discovery[{#SNMPVALUE},TRIPPLITE-PRODUCTS::tlpAtsOutletIndex]'
          key: tlpAtsOutletIndex
          delay: '86400'
          item_prototypes:
            -
              uuid: 466610c6f96948dfa55e8394ecabee2a
              name: 'Outlet - Ramp data type of outlet $1'
              type: SNMP_AGENT
              snmp_oid: '1.3.6.1.4.1.850.1.1.3.2.3.3.1.1.11.{#SNMPINDEX}'
              key: 'tlAtsOutletRampDataType[{#SNMPVALUE}]'
              delay: 1d
              history: '{$HISTORY}'
              trends: '{$TRENDS}'
              description: 'The type of data associated with ramp action.'
              valuemap:
                name: 'UPS Outlet Ramp Data Type'
              tags:
                -
                  tag: Application
                  value: PDU_OUTLETS_RAMP_DELAY
            -
              uuid: 510d8164c04545fe9e59d98619d29c14
              name: 'Outlet - Ndx group of outlet $1'
              type: SNMP_AGENT
              snmp_oid: '.1.3.6.1.4.1.850.1.1.3.4.3.3.1.1.14.1.{#SNMPINDEX}'
              key: 'tlpAtsOutletGroup[{#SNMPVALUE}]'
              delay: 1d
              history: '{$HISTORY}'
              trends: '{$TRENDS}'
              description: 'tlPDUOutletGroupIndex of corresponding outlet group, or 0 if ungrouped.'
              tags:
                -
                  tag: Application
                  value: PDU_OUTLETS_GROUP
            -
              uuid: 3d3a3949927840eb84eff100e0c4f97e
              name: 'Outlet - Name of outlet $1'
              type: SNMP_AGENT
              snmp_oid: '.1.3.6.1.4.1.850.1.1.3.4.3.3.1.1.2.1.{#SNMPINDEX}'
              key: 'tlpAtsOutletName[{#SNMPVALUE}]'
              delay: 1d
              history: '{$HISTORY}'
              trends: '0'
              value_type: CHAR
              description: 'A string identifying the devices attached to the output(s) of the device.'
              tags:
                -
                  tag: Application
                  value: PDU_OUTLETS_NAME
            -
              uuid: ceb6c67bcdcf418ea9e3bf4dbc0522b4
              name: 'Outlet - Ramp action of outlet $1'
              type: SNMP_AGENT
              snmp_oid: '.1.3.6.1.4.1.850.1.1.3.4.3.3.1.1.10.1.{#SNMPINDEX}'
              key: 'tlpAtsOutletRampAction[{#SNMPVALUE}]'
              delay: 1d
              history: '{$HISTORY}'
              trends: '{$TRENDS}'
              description: 'The ramp action to take on the Outlet.'
              valuemap:
                name: 'UPS Outlet Ramp Action'
              tags:
                -
                  tag: Application
                  value: PDU_OUTLETS_RAMP_ACTION
            -
              uuid: 9938fa470dc744bb8effaa306aa74da9
              name: 'Outlet - Shed action of outlet $1'
              type: SNMP_AGENT
              snmp_oid: '.1.3.6.1.4.1.850.1.1.3.4.3.3.1.1.12.1.{#SNMPINDEX}'
              key: 'tlpAtsOutletShedAction[{#SNMPVALUE}]'
              delay: 1d
              history: '{$HISTORY}'
              trends: '{$TRENDS}'
              description: 'The shed action to take on the Outlet.'
              valuemap:
                name: 'UPS Outlet Shed Action'
              tags:
                -
                  tag: Application
                  value: PDU_OUTLETS_SHAD_ACTION
            -
              uuid: 1a3a50337f674cfbb9ced48d7ffff417
              name: 'Outlet - Shed action data type of outlet $1'
              type: SNMP_AGENT
              snmp_oid: '1.3.6.1.4.1.850.1.1.3.2.3.3.1.1.13.{#SNMPINDEX}'
              key: 'tlpAtsOutletShedDataType[{#SNMPVALUE}]'
              delay: 1d
              history: '{$HISTORY}'
              trends: '{$TRENDS}'
              description: 'The type of data associated with shed action.'
              valuemap:
                name: 'UPS Outlet Shed Data Type'
              tags:
                -
                  tag: Application
                  value: PDU_OUTLETS_SHED_DELAY
            -
              uuid: 2d117ba88ba946789b7cb4887e9605c2
              name: 'Outlet - State of outlet $1'
              type: SNMP_AGENT
              snmp_oid: '.1.3.6.1.4.1.850.1.1.3.4.3.3.1.1.4.1.{#SNMPINDEX}'
              key: 'tlpAtsOutletState[{#SNMPVALUE}]'
              delay: 2m
              history: '{$HISTORY}'
              trends: '{$TRENDS}'
              description: 'The current state of the Outlet.'
              valuemap:
                name: 'UPS Outlet State'
              tags:
                -
                  tag: Application
                  value: PDU_OUTLETS_STATE
      macros:
        -
          macro: '{$MAX_INPUTVOLTAGE}'
          value: '125'
        -
          macro: '{$MAX_OUTPUTCURRENT_CRITICAL}'
          value: '12'
        -
          macro: '{$MAX_OUTPUTCURRENT_WARNING}'
          value: '10'
        -
          macro: '{$MIN_INPUTVOLTAGE}'
          value: '115'
        -
          macro: '{$SNMP_COMMUNITY}'
          value: zabbix
      valuemaps:
        -
          uuid: f5f4efa60cc04577ab38a75f6522fd41
          name: 'UPS Outlet Ramp Action'
          mappings:
            -
              value: '0'
              newvalue: remainOff
            -
              value: '1'
              newvalue: turnOnAfterDelay
        -
          uuid: 365b7c62f144488bac0d97080a5d449d
          name: 'UPS Outlet Ramp Data Type'
          mappings:
            -
              value: '0'
              newvalue: delayInSeconds
        -
          uuid: 448a0e35131f46f49752fac7e21853b8
          name: 'UPS Outlet Shed Action'
          mappings:
            -
              value: '0'
              newvalue: remainOn
            -
              value: '1'
              newvalue: turnOffAfterDelay
        -
          uuid: ec28afe345f342a29278e934d078dca1
          name: 'UPS Outlet Shed Data Type'
          mappings:
            -
              value: '0'
              newvalue: delayInSeconds
        -
          uuid: ce45bc011d5049c596a362ebb63cb852
          name: 'UPS Outlet State'
          mappings:
            -
              value: '0'
              newvalue: unknown
            -
              value: '1'
              newvalue: 'off'
            -
              value: '2'
              newvalue: 'on'
    -
      uuid: 37e5eb5606bc4abba66c8b20381a1e8a
      template: 'Template Module ICMP Ping'
      name: 'Template Module ICMP Ping'
      description: 'Template Module ICMP Ping version: 0.12'
      groups:
        -
          name: Templates/Modules
      items:
        -
          uuid: db5a94f6cea14deba957202b2f014469
          name: 'ICMP ping'
          type: SIMPLE
          key: icmpping
          delay: '60'
          history: 1w
          valuemap:
            name: 'Service state'
          tags:
            -
              tag: Application
              value: Status
          triggers:
            -
              uuid: b030876299434f3ba43e11c584104a81
              expression: 'max(/Template Module ICMP Ping/icmpping,#3)=0'
              name: 'Unavailable by ICMP ping'
              priority: HIGH
              description: |
                Last value: {ITEM.LASTVALUE1}.
                Last three attempts returned timeout.  Please check device connectivity.
        -
          uuid: 04b21adaf422473a88df2c52786474ed
          name: 'ICMP loss'
          type: SIMPLE
          key: icmppingloss
          delay: '60'
          history: 1w
          value_type: FLOAT
          units: '%'
          tags:
            -
              tag: Application
              value: Status
          triggers:
            -
              uuid: 42c4b0310aaf4b9c8cb502542b7dea90
              expression: 'min(/Template Module ICMP Ping/icmppingloss,5m)>{$ICMP_LOSS_WARN} and min(/Template Module ICMP Ping/icmppingloss,5m)<100'
              name: 'High ICMP ping loss'
              priority: WARNING
              dependencies:
                -
                  name: 'Unavailable by ICMP ping'
                  expression: 'max(/Template Module ICMP Ping/icmpping,#3)=0'
        -
          uuid: a79e33e5fd264725b934f603fa071555
          name: 'ICMP response time'
          type: SIMPLE
          key: icmppingsec
          delay: '60'
          history: 1w
          value_type: FLOAT
          units: s
          tags:
            -
              tag: Application
              value: Status
          triggers:
            -
              uuid: 32b4d8f3eba34bd380803410111d4b7f
              expression: 'avg(/Template Module ICMP Ping/icmppingsec,5m)>{$ICMP_RESPONSE_TIME_WARN}'
              name: 'High ICMP ping response time'
              priority: WARNING
              dependencies:
                -
                  name: 'High ICMP ping loss'
                  expression: 'min(/Template Module ICMP Ping/icmppingloss,5m)>{$ICMP_LOSS_WARN} and min(/Template Module ICMP Ping/icmppingloss,5m)<100'
                -
                  name: 'Unavailable by ICMP ping'
                  expression: 'max(/Template Module ICMP Ping/icmpping,#3)=0'
      macros:
        -
          macro: '{$ICMP_LOSS_WARN}'
          value: '20'
        -
          macro: '{$ICMP_RESPONSE_TIME_WARN}'
          value: '0.15'
      valuemaps:
        -
          uuid: bdb5d65d925542eaa61c302dc40fbfe8
          name: 'Service state'
          mappings:
            -
              value: '0'
              newvalue: Down
            -
              value: '1'
              newvalue: Up
  graphs:
    -
      uuid: fdf835a570274271a03a6184f74df3d6
      name: 'Input Frecuency'
      yaxismax: '80'
      ymin_type_1: FIXED
      ymax_type_1: FIXED
      graph_items:
        -
          color: F6C800
          item:
            host: 'SNMP Tripp Lite PDU 15'
            key: tlpAtsInputPhaseFrequency
    -
      uuid: 2ce6ca01d387448bb3cd180065fd52c9
      name: 'Input Voltage'
      yaxismax: '120'
      ymin_type_1: FIXED
      ymax_type_1: FIXED
      graph_items:
        -
          color: F63100
          item:
            host: 'SNMP Tripp Lite PDU 15'
            key: tlpAtsInputPhaseVoltage
    -
      uuid: 8544f4a3948140a38de897f12f7b7625
      name: 'Output Current'
      yaxismax: '50'
      ymin_type_1: FIXED
      ymax_type_1: FIXED
      graph_items:
        -
          drawtype: FILLED_REGION
          color: FF3333
          item:
            host: 'SNMP Tripp Lite PDU 15'
            key: tlpAtsOutputCurrent
